{"columns":[{"name":"edb","type":"string"},{"name":"disc_yr","type":"double"},{"name":"subnetwork","type":"string"},{"name":"table_description","type":"string"},{"name":"row_num","type":"double"},{"name":"rank","type":"string"},{"name":"feeder","type":"string"},{"name":"table_value","type":"double"},{"name":"number_of_unplanned_interruptions","type":"double"},{"name":"most_common_cause","type":"string"},{"name":"circuit_length_of_feeder","type":"double"},{"name":"number_of_icps","type":"double"},{"name":"percent_of_feeder_overhead","type":"double"},{"name":"section","type":"string"},{"name":"sect_no","type":"double"},{"name":"source","type":"string"},{"name":"schedule","type":"string"}],"n_rows":1602,"rows_kept":1602,"cut":false,"text_format":"parquet-jsonl-2026-10-02","bounds":{"document_bytes":16777216,"package_text_limit_bytes":33554432,"package_text_slack_bytes":1024,"rows_first":2000,"rows_last":500,"rows_between":2000,"halvings":0,"cell_chars":16384,"cell_head_chars":4096,"vector_min":64,"vector_head_fixed":16,"vector_head_variable":64,"kv_value_chars":1048576,"nesting_max":64,"binary_text":true},"cells_cut":0,"cells_bad_utf8":0,"cells_raw":0,"cells_binary":0,"cells_binary_text":0,"cells_vector":0,"n_row_groups":1,"reader":"pyarrow 23.0.1, python 3.13","created_by":"parquet-cpp-arrow version 21.0.0","schema":{"fields":[{"name":"edb","type":"string","nullable":true,"metadata":null,"children":null},{"name":"disc_yr","type":"double","nullable":true,"metadata":null,"children":null},{"name":"subnetwork","type":"string","nullable":true,"metadata":null,"children":null},{"name":"table_description","type":"string","nullable":true,"metadata":null,"children":null},{"name":"row_num","type":"double","nullable":true,"metadata":null,"children":null},{"name":"rank","type":"string","nullable":true,"metadata":null,"children":null},{"name":"feeder","type":"string","nullable":true,"metadata":null,"children":null},{"name":"table_value","type":"double","nullable":true,"metadata":null,"children":null},{"name":"number_of_unplanned_interruptions","type":"double","nullable":true,"metadata":null,"children":null},{"name":"most_common_cause","type":"string","nullable":true,"metadata":null,"children":null},{"name":"circuit_length_of_feeder","type":"double","nullable":true,"metadata":null,"children":null},{"name":"number_of_icps","type":"double","nullable":true,"metadata":null,"children":null},{"name":"percent_of_feeder_overhead","type":"double","nullable":true,"metadata":null,"children":null},{"name":"section","type":"string","nullable":true,"metadata":null,"children":null},{"name":"sect_no","type":"double","nullable":true,"metadata":null,"children":null},{"name":"source","type":"string","nullable":true,"metadata":null,"children":null},{"name":"schedule","type":"string","nullable":true,"metadata":null,"children":null}],"parquet":"required group field_id=-1 schema {\n  optional binary field_id=-1 edb (String);\n  optional double field_id=-1 disc_yr;\n  optional binary field_id=-1 subnetwork (String);\n  optional binary field_id=-1 table_description (String);\n  optional double field_id=-1 row_num;\n  optional binary field_id=-1 rank (String);\n  optional binary field_id=-1 feeder (String);\n  optional double field_id=-1 table_value;\n  optional double field_id=-1 number_of_unplanned_interruptions;\n  optional binary field_id=-1 most_common_cause (String);\n  optional double field_id=-1 circuit_length_of_feeder;\n  optional double field_id=-1 number_of_icps;\n  optional double field_id=-1 percent_of_feeder_overhead;\n  optional binary field_id=-1 section (String);\n  optional double field_id=-1 sect_no;\n  optional binary field_id=-1 source (String);\n  optional binary field_id=-1 schedule (String);\n}\n"},"kv_metadata":[["ARROW:schema",{"$cut":{"chars":2112,"head":""}}],["r","A\n3\n263425\n197888\n5\nUTF-8\n531\n1\n531\n17\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n254\n1026\n1\n262153\n5\nnames\n16\n17\n262153\n3\nedb\n262153\n7\ndisc_yr\n262153\n10\nsubnetwork\n262153\n17\ntable_description\n262153\n7\nrow_num\n262153\n4\nrank\n262153\n6\nfeeder\n262153\n11\ntable_value\n262153\n33\nnumber_of_unplanned_interruptions\n262153\n17\nmost_common_cause\n262153\n24\ncircuit_length_of_feeder\n262153\n14\nnumber_of_icps\n262153\n26\npercent_of_feeder_overhead\n262153\n7\nsection\n262153\n7\nsect_no\n262153\n6\nsource\n262153\n8\nschedule\n254\n1026\n511\n16\n1\n262153\n7\ncolumns\n254\n"]]}
["Alpine Energy",2025.0,null,"SAIDI",12.0,"1","Geraldine Township",11.997612309206453,18.0,"Defective equipment",26.0,1408.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",13.0,"2","Hadlow",7.406997995476604,25.0,"Defective equipment",163.0,888.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",14.0,"3","Woodbury",7.269248909312716,28.0,"Lightning",153.0,687.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",15.0,"4","Temuka East",5.540797076052589,2.0,"Defective equipment",19.0,1397.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",16.0,"5","Cave",5.425598396367795,40.0,"Adverse weather",208.0,397.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",17.0,"6","Normanby",5.42344652766363,18.0,"Third party interference",73.74314646549036,546.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",18.0,"7","Rolleston Road",4.643055064195635,21.0,"Defective equipment",36.241808492384955,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",19.0,"8","Waihaorunga",4.308690013046297,11.0,"Defective equipment",22.052558611210912,241.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",20.0,"9","Fairlie Rural",4.287849310389485,24.0,"Defective equipment",212.46706031812047,674.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",21.0,"10","Totara Valley",4.287760877058489,12.0,"Third party interference",69.3293035586472,546.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",22.0,"11","Otaio",3.9430786463739276,16.0,"Defective equipment",115.59726825601285,320.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",23.0,"12","Morven",3.883474826051165,29.0,"Wildlife",111.16854708002623,311.5172413793103,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",24.0,"13","Waitohi",3.872450182801418,12.0,"Third party interference",102.43355845403649,286.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIDI",25.0,"14","Tawai",3.475887277375743,12.0,"Third party interference",54.239241441989705,317.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",30.0,"1","Geraldine Township",0.15287112368824432,18.0,"Defective equipment",26.0,1408.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",31.0,"2","Waihaorunga",0.08421766301143734,11.0,"Defective equipment",22.052558611210912,241.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",32.0,"3","Normanby",0.05972173092795661,18.0,"Third party interference",73.74314646549036,546.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",33.0,"4","Totara Valley",0.05869001297016861,12.0,"Third party interference",69.3293035586472,546.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",34.0,"5","Hadlow",0.054769484730574226,25.0,"Defective equipment",163.0,888.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",35.0,"6","Rolleston Road",0.052204928664072635,21.0,"Defective equipment",36.241808492384955,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",36.0,"7","Fairlie Rural",0.04571984435797665,24.0,"Defective equipment",212.46706031812047,674.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",37.0,"8","Tawai",0.04330267657115906,12.0,"Third party interference",54.239241441989705,317.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",38.0,"9","Temuka East",0.043066855323664666,2.0,"Defective equipment",19.0,1397.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",39.0,"10","Cave",0.04244782454899186,40.0,"Adverse weather",208.0,397.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",40.0,"11","Morven",0.03917580474000708,29.0,"Wildlife",111.16854708002623,311.5172413793103,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",41.0,"12","Otaio",0.03846834099752388,16.0,"Defective equipment",115.59726825601285,320.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",42.0,"13","Grants Road",0.03528475415634949,3.0,"Third party interference",8.0,1116.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"SAIFI",43.0,"14","Woodbury",0.027738474236528712,28.0,"Lightning",153.0,687.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",48.0,"1","Rolleston Road",157510.9999977727,21.0,"Defective equipment",36.241808492384955,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",49.0,"2","Waikakahi",1189.9010988976934,20.0,"Lightning",141.80056917844286,91.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",50.0,"3","Waihaorunga",606.5062240771061,11.0,"Defective equipment",22.052558611210912,241.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",51.0,"4","M159",599.8823529354515,6.0,"Defective equipment",5.0,68.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",52.0,"5","M158",523.1333333272487,3.0,"Cause unknown",5.0,15.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",53.0,"6","Mahan Road",506.666666672565,6.0,"Defective equipment",33.0,90.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",54.0,"7","Rangitata",500.8791946356213,22.0,"Cause unknown",48.0,149.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",55.0,"8","Cave",463.6221662427736,40.0,"Adverse weather",208.0,397.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",56.0,"9","Waitohi",459.33216783690665,12.0,"Third party interference",102.43355845403649,286.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",57.0,"10","Morven",422.9075713936055,29.0,"Wildlife",111.16854708002623,311.5172413793103,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",58.0,"11","Otaio",418.01562499871596,16.0,"Defective equipment",115.59726825601285,320.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",59.0,"12","Tawai",371.97476339966784,12.0,"Third party interference",54.239241441989705,317.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",60.0,"13","Woodbury",358.95487627296154,28.0,"Lightning",153.0,687.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Alpine Energy",2025.0,null,"Customer impact",61.0,"14","Normanby",336.9688644770348,18.0,"Third party interference",73.74314646549036,546.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIDI",12.0,"1","CB168",49.520200229429534,26.0,"Defective equipment",168.94316444391546,1121.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIDI",12.0,"1","CB5310",15.800941006152732,3.0,"Human error",5.407247273950991,219.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",12.0,"1","CB168",12.340412482587988,26.0,"Defective equipment",168.94316444391546,1121.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",12.0,"1","PC3",5.040540777499168,8.0,"Defective equipment",61.58269867885671,529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",13.0,"2","CB2006",8.337709723694879,28.0,"Defective equipment",129.8019959887479,1124.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",13.0,"2","WS4",2.063844710585843,5.0,"Adverse Environment",15.40763356806857,304.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIDI",13.0,"2","CB2006",33.457962248409636,28.0,"Defective equipment",129.8019959887479,1124.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIDI",13.0,"2","CB7632",8.95897081564834,17.0,"Defective equipment",121.80338992430408,632.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIDI",14.0,"3","CB656",29.066013140056317,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIDI",14.0,"3","CB5309",8.31309841081828,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",14.0,"3","CB656",7.243237905153952,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",14.0,"3","ET2",2.0428027845482126,7.0,"Vegetation",43.6227072122902,592.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",15.0,"4","CB2423",3.5761242437472722,12.0,"Defective equipment",125.70795189632148,389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",15.0,"4","OT3",1.726349751880622,10.0,"Defective equipment",55.13226300480183,230.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIDI",15.0,"4","CB7652",7.24844536570921,6.0,"Human error",52.32472409169521,547.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIDI",15.0,"4","CB2423",14.350443216185214,12.0,"Defective equipment",125.70795189632148,389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",16.0,"5","CB480",3.3405788062121875,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",16.0,"5","HB13",1.5676059548650687,2.0,"Vegetation",21.692244852082887,672.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIDI",16.0,"5","CB480",13.405235165293568,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",17.0,"6","PC3",2.9881806274558724,8.0,"Defective equipment",61.58269867885671,529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",17.0,"6","OT2",1.1178347858107278,5.0,"Human error",39.74101840342635,313.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",18.0,"7","CB2755",2.794403210045947,4.0,"Wildlife",60.43300948351009,913.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",18.0,"7","GI10",1.0870960388574233,6.0,"Third-party Interference",28.672964755232588,702.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",19.0,"8","CB5310",2.4960913948314936,3.0,"Human error",5.407247273950991,219.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",19.0,"8","HB1",1.0289501832401058,4.0,"Human error",30.894289821221363,649.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",20.0,"9","CO7",0.9879359624050921,5.0,"Defective equipment",24.772061677770417,485.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",20.0,"9","CB2758",2.0393667228008896,6.0,"Defective equipment",52.33988934117596,1179.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIFI",20.0,"1","CB5309",0.1806995031750732,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",21.0,"10","CB167",2.0359155075989106,7.0,"Human error",22.868366150862634,905.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIFI",21.0,"1","CB168",0.43307957034101563,26.0,"Defective equipment",168.94316444391546,1121.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIFI",21.0,"2","CB5310",0.17951501990589938,3.0,"Human error",5.407247273950991,219.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",21.0,"10","GI2",0.9456241561310912,8.0,"Defective equipment",9.825599442455648,215.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIFI",22.0,"2","CB2006",0.3454791949108353,28.0,"Defective equipment",129.8019959887479,1124.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",22.0,"11","OT1",0.7915797225972749,8.0,"Defective equipment",26.196566135155518,110.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",22.0,"11","CB821",2.0343978045281608,8.0,"Human error",102.60784607847198,778.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIFI",22.0,"3","CB7784",0.1753035238377258,6.0,"Human error",118.52941616405336,1599.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","SAIFI",23.0,"4","CB7652",0.1747770868292041,6.0,"Human error",52.32472409169521,547.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",23.0,"12","CB832",1.9031164889082932,7.0,"Human error",120.92935234405834,1424.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIFI",23.0,"3","CB656",0.23689644384190217,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",23.0,"12","CO11",0.7540374195584703,1.0,"Defective equipment",11.252799422154082,440.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",24.0,"13","PC4",0.7213522944466849,8.0,"Adverse Environment",53.70941561672482,783.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",24.0,"13","CB838",1.6045343978045281,4.0,"Defective equipment",17.894466386498294,544.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIFI",24.0,"4","CB480",0.17157159244968193,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",25.0,"14","ET3",0.5447579301758755,6.0,"Defective equipment",65.21529318330732,783.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","SAIFI",25.0,"5","CB2755",0.15309208468036287,4.0,"Wildlife",60.43300948351009,913.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",25.0,"14","CB2752",1.4780037007006384,10.0,"Third-party Interference",156.07193248925574,1523.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",26.0,"15","CB7632",1.4152581134742928,17.0,"Defective equipment",121.80338992430408,632.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",26.0,"15","WB11",0.5255922425432675,5.0,"Defective equipment",3.086968455089612,188.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",27.0,"16","CB6576",1.4122850786918646,14.0,"Wildlife",99.3837805723679,220.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIDI",27.0,"16","AB7",0.47019937224920655,1.0,"Cause Unknown",30.607465259832807,694.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","Customer impact",28.0,"1","CB710",1691.0,1.0,"Defective equipment",0.846434696103551,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",28.0,"17","CB5309",1.3132289652591531,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","Customer impact",29.0,"2","CB5272",540.9090909090909,1.0,"Human error",2.93006490238295,77.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",29.0,"18","CB4635",1.2576352938730535,4.0,"Vegetation",34.59928997663315,223.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",30.0,"19","WS4",1.2235077652342046,5.0,"Adverse Environment",15.40763356806857,304.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","Customer impact",30.0,"1","CB2084",1147.5066666666667,21.0,"Cause Unknown",78.0519837086308,150.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","Customer impact",30.0,"3","CB5309",243.41542625169149,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","Customer impact",31.0,"2","CB2423",565.8562259306804,12.0,"Defective equipment",125.70795189632148,389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Queenstown","Customer impact",31.0,"4","CB7830",227.8625,9.0,"Defective equipment",11.94986163950315,80.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",31.0,"20","ET2",1.2110334934198217,7.0,"Vegetation",43.6227072122902,592.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",32.0,"21","CB7652",1.1450445955217365,6.0,"Human error",52.32472409169521,547.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",32.0,"1","PC3",0.032211681775938555,8.0,"Defective equipment",61.58269867885671,529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","Customer impact",32.0,"3","CB656",481.40697674418607,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",33.0,"2","GI2",0.03008995423381087,8.0,"Defective equipment",9.825599442455648,215.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",33.0,"22","CB2084",1.1090459261107295,21.0,"Cause Unknown",78.0519837086308,150.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","Customer impact",33.0,"4","HSB33",369.3333333333333,9.0,"Cause Unknown",0.0199416890458,6.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",34.0,"3","ET9",0.029002788055199985,5.0,"Third-party Interference",41.50806289177736,1541.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",34.0,"23","CB169",1.1075698039460278,14.0,"Defective equipment",91.34847537071593,302.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Central Otago","Customer impact",34.0,"5","CB480",350.75728155339806,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",35.0,"4","GI10",0.02647775693068439,6.0,"Third-party Interference",28.672964755232588,702.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIDI",35.0,"24","CB190",1.0855111332875944,3.0,"Human error",24.862113621041324,657.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",36.0,"5","HB13",0.02363709691560434,2.0,"Vegetation",21.692244852082887,672.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",37.0,"6","ET2",0.020340528503042313,7.0,"Vegetation",43.6227072122902,592.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",38.0,"7","OT3",0.019586526153360567,10.0,"Defective equipment",55.13226300480183,230.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",39.0,"8","CO11",0.018201266022549928,1.0,"Defective equipment",11.252799422154082,440.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",40.0,"1","CB168",0.1079232416474355,26.0,"Defective equipment",168.94316444391546,1121.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",40.0,"9","OT2",0.017499868487962266,5.0,"Human error",39.74101840342635,313.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",41.0,"2","CB2006",0.08609326597226552,28.0,"Defective equipment",129.8019959887479,1124.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",41.0,"10","PC4",0.014676743411246909,8.0,"Adverse Environment",53.70941561672482,783.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",42.0,"3","CB656",0.059034491361566785,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",42.0,"11","PC7",0.013747391677918252,2.0,"Defective equipment",44.542038990674335,764.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",43.0,"4","CB480",0.04275556664379718,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",43.0,"12","GI3",0.01371232180118887,3.0,"Human error",26.72705141192902,773.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",44.0,"5","CB2755",0.03815048129898751,4.0,"Wildlife",60.43300948351009,913.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",44.0,"13","WB11",0.013238878465342196,5.0,"Defective equipment",3.086968455089612,188.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",45.0,"6","CB2423",0.03771388178548411,12.0,"Defective equipment",125.70795189632148,389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",45.0,"14","HB1",0.012590085745848602,4.0,"Human error",30.894289821221363,649.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",46.0,"7","CB2758",0.032464292396931334,6.0,"Defective equipment",52.33988934117596,1179.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",46.0,"15","WS4",0.010976871416296972,5.0,"Adverse Environment",15.40763356806857,304.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",47.0,"8","CB190",0.031850974032724175,3.0,"Human error",24.862113621041324,657.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","SAIFI",47.0,"16","CO9",0.01074891721755598,1.0,"Defective equipment",11.142615645822463,596.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",48.0,"9","CB5309",0.028545292001912727,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",49.0,"10","CB5310",0.02835817792469698,3.0,"Human error",5.407247273950991,219.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",50.0,"11","CB7784",0.027692883427929894,6.0,"Human error",118.52941616405336,1599.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",51.0,"12","CB7652",0.027609721615834006,6.0,"Human error",52.32472409169521,547.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",52.0,"1","HSB33",369.3333333333333,9.0,"Cause Unknown",0.0199416890458,6.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",52.0,"13","CB821",0.0260192519595002,8.0,"Human error",102.60784607847198,778.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",53.0,"14","CB4637",0.02563462857855673,6.0,"Vegetation",20.69387350775982,482.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",53.0,"2","OT1",233.02727272727273,8.0,"Defective equipment",26.196566135155518,110.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",54.0,"15","CB2757",0.025198029065053328,1.0,"Human error",50.81513630002433,1203.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",54.0,"3","GI4",194.47826086956522,3.0,"Third-party Interference",5.088061580715653,23.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",55.0,"16","CB167",0.02090480051560324,7.0,"Human error",22.868366150862634,905.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",55.0,"4","GI2",175.10697674418606,8.0,"Defective equipment",9.825599442455648,215.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",56.0,"5","SC1",156.8,1.0,"Defective equipment",2.797645661844077,67.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",56.0,"17","CB838",0.02050978190814778,4.0,"Defective equipment",17.894466386498294,544.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",57.0,"18","CB2752",0.019563816295557084,10.0,"Third-party Interference",156.07193248925574,1523.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",57.0,"6","OT3",128.2478260869565,10.0,"Defective equipment",55.13226300480183,230.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",58.0,"7","OT2",125.21725239616613,5.0,"Human error",39.74101840342635,313.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",58.0,"19","PC3",0.019096031102517723,8.0,"Defective equipment",61.58269867885671,529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",59.0,"20","CB7782",0.01859706022994241,11.0,"Human error",99.69555728590372,1108.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",59.0,"8","WB11",119.82978723404256,5.0,"Defective equipment",3.086968455089612,188.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",60.0,"21","CB7632",0.018274808208070856,17.0,"Defective equipment",121.80338992430408,632.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",60.0,"9","CO7",112.89896907216495,5.0,"Defective equipment",24.772061677770417,485.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",61.0,"10","PC3",89.94517958412098,8.0,"Defective equipment",61.58269867885671,529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",61.0,"22","CB5730",0.01806690367783114,8.0,"Defective equipment",18.09088129005317,882.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",62.0,"11","WS8",70.3768115942029,2.0,"Adverse Environment",7.551588945956873,241.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",62.0,"23","GI2",0.017838208694567457,8.0,"Defective equipment",9.825599442455648,215.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",63.0,"12","ET2",70.33586497890295,7.0,"Vegetation",43.6227072122902,592.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"SAIFI",63.0,"24","ET9",0.017193704650824343,5.0,"Third-party Interference",41.50806289177736,1541.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",64.0,"13","GI10",65.16298932384342,6.0,"Third-party Interference",28.672964755232588,702.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",65.0,"14","SC4",42.37918215613383,2.0,"Defective equipment",4.475147508217861,134.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",66.0,"15","ET3",39.676883780332055,6.0,"Defective equipment",65.21529318330732,783.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,"Dunedin","Customer impact",67.0,"16","AB7",38.638328530259365,1.0,"Cause Unknown",30.607465259832807,694.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",68.0,"1","CB710",1691.0,1.0,"Defective equipment",0.846434696103551,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",69.0,"2","CB2084",1147.5066666666667,21.0,"Cause Unknown",78.0519837086308,150.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",70.0,"3","CB2423",565.8562259306804,12.0,"Defective equipment",125.70795189632148,389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",71.0,"4","CB5272",540.9090909090909,1.0,"Human error",2.93006490238295,77.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",72.0,"5","CB656",481.40697674418607,53.0,"Defective equipment",257.45441665235774,688.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",73.0,"6","HSB33",369.3333333333333,9.0,"Cause Unknown",0.0199416890458,6.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",74.0,"7","CB480",350.75728155339806,28.0,"Vegetation",114.41451635865337,412.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",75.0,"8","CB4633",348.03636363636366,7.0,"Defective equipment",24.84646376751741,55.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",76.0,"9","CB6576",343.0249433106576,14.0,"Wildlife",99.3837805723679,220.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",77.0,"10","CB168",328.5786892554614,26.0,"Defective equipment",168.94316444391546,1121.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",78.0,"11","CB4639",267.1803278688525,8.0,"Defective equipment",35.36208048584661,122.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",79.0,"12","CB4635",263.6152125279642,4.0,"Vegetation",34.59928997663315,223.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",80.0,"13","CB5309",243.41542625169149,5.0,"Human error",11.14016964142166,369.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",81.0,"14","OT1",233.02727272727273,8.0,"Defective equipment",26.196566135155518,110.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",82.0,"15","CB7830",227.8625,9.0,"Defective equipment",11.94986163950315,80.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",83.0,"16","CB167",216.4099447513812,7.0,"Human error",22.868366150862634,905.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",84.0,"17","CB7783",199.0,3.0,"Human error",0.07301951956489,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",85.0,"18","GI4",194.47826086956522,3.0,"Third-party Interference",5.088061580715653,23.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",86.0,"19","CB199",190.02777777777777,3.0,"Defective equipment",7.6856300722806,36.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",87.0,"20","CB2006",188.27301022676744,28.0,"Defective equipment",129.8019959887479,1124.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",88.0,"21","GI2",175.10697674418606,8.0,"Defective equipment",9.825599442455648,215.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",89.0,"22","CB192",172.0373831775701,6.0,"Defective equipment",28.923387357019507,107.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",90.0,"23","CB2881",169.92727272727274,2.0,"Wildlife",17.89297452301342,27.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Aurora Energy",2025.0,null,"Customer impact",91.0,"24","SC1",156.8,1.0,"Defective equipment",2.797645661844077,67.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Buller Electricity",2025.0,null,"SAIDI",12.0,"1","28-WHA",22.2136785380696,13.0,"Unknown",74.6,561.0,100.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Buller Electricity",2025.0,null,"SAIFI",20.0,"1","28-WHA",0.200405268490375,13.0,"Unknown",74.6,561.0,100.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Buller Electricity",2025.0,null,"Customer impact",28.0,"1","60-LIT",273.68,4.0,"Defective Equipment",19.1,125.0,100.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIDI",12.0,"1","46 - Cooks Tooth/Herbertville",11.129418550647411,16.0,"Unknown",173.8645054038126,376.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIDI",13.0,"2","15 - Waipukurau CBD",7.642144835402569,3.0,"Defective equipment",52.97246888850247,895.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIDI",14.0,"3","45 - Porangahau/Wallingford",7.515012031438163,12.0,"Unknown",135.78702538095402,437.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIFI",19.0,"1","45 - Porangahau/Wallingford",0.3580753450205148,12.0,"Unknown",135.78702538095402,437.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIFI",20.0,"2","46 - Cooks Tooth/Herbertville",0.32216124047530226,16.0,"Unknown",173.8645054038126,376.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"SAIFI",21.0,"3","19 - Hatuma/Wanstead",0.18937496669686146,8.0,"Defective equipment",220.29813797866487,672.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"Customer impact",26.0,"1","46 - Cooks Tooth/Herbertville",277.37821771580343,16.0,"Unknown",173.8645054038126,376.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"Customer impact",27.0,"2","45 - Porangahau/Wallingford",161.18197805028572,12.0,"Unknown",135.78702538095402,437.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Centralines",2025.0,null,"Customer impact",28.0,"3","74 - Takapau Urban/Otawhao",153.10856317741934,6.0,"Defective equipment",91.88055476600667,434.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIDI",12.0,"1","Kaiaua",18.347679194781445,23.0,"Defective Equipment",101.76952000000007,1075.0,0.9377467831232771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIDI",13.0,"2","Pukekohe West",7.07856272838003,1.0,"Vegetation",12.55184,3014.0,0.3880785605935065,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIDI",14.0,"3","Manukau Heads",6.641903571078274,29.0,"Defective Equipment",106.00889999999997,964.0,0.9760322954016125,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIDI",15.0,"4","Blackbridge",5.2152308370535305,6.0,"Defective Equipment",44.22493,583.0,0.8033342280021698,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIDI",16.0,"5","Drury",4.991882450416845,13.0,"Cause Unknown",41.12991999999999,1588.0,0.6534094887614662,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIFI",21.0,"1","Manukau Heads",0.18597472612591603,29.0,"Defective Equipment",106.00889999999997,964.0,0.9760322954016125,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIFI",22.0,"2","Kaiaua",0.1718303143185651,23.0,"Defective Equipment",101.76952000000007,1075.0,0.9377467831232771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIFI",23.0,"3","Drury",0.11331977224648426,13.0,"Cause Unknown",41.12991999999999,1588.0,0.6534094887614662,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIFI",24.0,"4","Waiau Pa",0.10675377091599167,10.0,"Defective Equipment",36.5667,1541.0,0.6862880708404095,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"SAIFI",25.0,"5","Pukekohe West",0.0904993909866017,1.0,"Vegetation",12.55184,3014.0,0.3880785605935065,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"Customer impact",30.0,"1","Kaiaua",828.8139534883721,23.0,"Defective Equipment",101.76952000000007,1075.0,0.9377467831232771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"Customer impact",31.0,"2","Blackbridge",435.2006861063465,6.0,"Defective Equipment",44.22493,583.0,0.8033342280021698,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"Customer impact",32.0,"4","Manukau Heads",338.451244813278,29.0,"Defective Equipment",106.00889999999997,964.0,0.9760322954016125,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"Customer impact",33.0,"4","Whangarata",291.90909090909093,6.0,"Wildlife",106.00889999999997,964.0,0.9760322954016125,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Counties Energy",2025.0,null,"Customer impact",34.0,"5","Otaua",290.73655913978496,13.0,"Defective Equipment",59.18741000000004,558.0,0.9973518016753902,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",12.0,"1","NV05 Carew_22",4.452549276651529,14.0,"Wildlife",71.54135200000006,288.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",13.0,"2","TF59 Carters Terrace_11",3.458682522590009,3.0,"Unknown",31.93769299999999,801.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",14.0,"3","OW04 Rakaia_22",3.21236949295379,2.0,"Unknown and Defective Equipment",37.009016000000074,676.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",15.0,"4","YV05 Longbeach_22",2.6779343602228565,9.0,"Defective Equipment",44.014062999999965,216.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",16.0,"5","MU06 Blackford Rd East_11",2.6042417716185216,4.0,"Third Party Interference",55.48,106.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",17.0,"6","SX03 Ashburton Gorge_22",2.5566740015918348,6.0,"Vegetation",7.670831999999998,115.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",18.0,"7","YW04 Flemington_22",2.3756261997284516,6.0,"Unknown",72.05104200000002,421.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",19.0,"8","UW04 Braemar_22",2.2736551336673063,11.0,"Unknown",77.76771899999997,388.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",20.0,"9","NT07 Stoneylea Rd_22",2.267849618427829,13.0,"Unknown",32.33677299999996,133.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",21.0,"10","WY02 Hakatere_22",2.2102626527459153,3.0,"Defective Equipment",42.771077,247.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIDI",22.0,"11","OX03 Hatfield_22",1.9689592209373097,7.0,"Defective Equipment",51.57961300000005,258.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",27.0,"1","TF59 Carters Terrace_11",0.11742122758556112,3.0,"Unknown",31.93769299999999,801.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",28.0,"2","OW04 Rakaia_22",0.062456107495669266,2.0,"Unknown and Defective Equipment",37.009016000000074,676.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",29.0,"3","NV05 Carew_22",0.04644412191582002,14.0,"Wildlife",71.54135200000006,288.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",30.0,"4","OX03 Hatfield_22",0.04199634814363968,7.0,"Defective Equipment",51.57961300000005,258.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",31.0,"5","YV05 Longbeach_22",0.0352076408071539,9.0,"Defective Equipment",44.014062999999965,216.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",32.0,"6","JW04 Coldstream_22",0.031789877803267946,4.0,"Defective Equipment",38.94594700000005,298.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",33.0,"7","FH19 Mitcham Rd_22",0.030010768294395807,5.0,"Unknown",39.13264899999995,249.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",34.0,"8","RY02 Rakaia Huts_22",0.026593005290509855,8.0,"Defective Equipment",34.64080399999997,195.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",35.0,"9","UW04 Braemar_22",0.026546186619223745,11.0,"Unknown",77.76771899999997,388.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",36.0,"10","GY02 Ferrimans Rd_22",0.02612481857764877,8.0,"Wildlife",62.9264500000001,274.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"SAIFI",37.0,"11","SX03 Ashburton Gorge_22",0.024345709068776627,6.0,"Vegetation",7.670831999999998,115.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",42.0,"1","AE96 Upper Rakaia_11",758.1333333333333,5.0,"Lightning and Unknown",21.67745,15.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",43.0,"2","MU06 Blackford Rd East_11",524.7547169811321,4.0,"Third Party Interference",55.48,106.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",44.0,"3","SX03 Ashburton Gorge_22",472.79653679653677,6.0,"Vegetation",7.670831999999998,115.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",45.0,"4","NT07 Stoneylea Rd_22",362.83895131086143,13.0,"Unknown",32.33677299999996,133.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",46.0,"5","MT07 Blackford Rd West_11",342.8421052631579,2.0,"Third Party Interference and Unknown",5.76,19.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",47.0,"6","NV05 Carew_22",329.64298093587524,14.0,"Wildlife",71.54135200000006,288.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",48.0,"7","YV05 Longbeach_22",264.19399538106234,9.0,"Defective Equipment",44.014062999999965,216.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",49.0,"8","YX03 Lynnford_22",244.90419161676647,2.0,"Defective Equipment",40.156774999999904,167.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",50.0,"9","PV05 Christys Rd_22",242.05208333333334,2.0,"Defective Equipment",24.746607999999974,96.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",51.0,"10","UY02 Barrhill_22",225.50310559006212,4.0,"Defective Equipment",45.74583900000002,161.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["EA Networks",2025.0,null,"Customer impact",52.0,"11","RW04 Dorie East_22",210.7982062780269,4.0,"Defective Equipment",28.09857799999995,111.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIDI",12.0,"1","E150",8.7679,8.0,"Lightning",35.9,1189.0,0.74,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIDI",13.0,"2","402",8.2668,3.0,"Defective Equipment",10.0,1862.0,0.3,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIDI",14.0,"3","C4",7.6659,14.0,"Defective Equipment",36.9,1431.0,0.81,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIDI",15.0,"4","E153",2.5615,11.0,"Cause Unknown",37.5,736.0,0.93,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIDI",16.0,"5","682",2.5376,1.0,"Third Party Interference",10.8,765.0,0.16,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIFI",21.0,"1","C4",0.0985,14.0,"Defective Equipment",36.9,1431.0,0.81,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIFI",22.0,"2","402",0.0857,3.0,"Defective Equipment",10.0,1862.0,0.3,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIFI",23.0,"3","E153",0.0818,11.0,"Cause Unknown",37.5,736.0,0.93,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIFI",24.0,"4","G313",0.0774,6.0,"Cause Unknown",46.1,750.0,0.87,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"SAIFI",25.0,"5","G310",0.0577,2.0,"Human Error",9.7,1399.0,0.41,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"Customer impact",30.0,"1","E150",345.99,8.0,"Lightning",35.9,1189.0,0.74,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"Customer impact",31.0,"2","C4",251.35,14.0,"Defective Equipment",36.9,1431.0,0.81,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"Customer impact",32.0,"3","402",208.31,3.0,"Defective Equipment",10.0,1862.0,0.3,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"Customer impact",33.0,"4","E153",163.29,11.0,"Cause Unknown",37.5,736.0,0.93,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electra",2025.0,null,"Customer impact",34.0,"5","682",155.64,1.0,"Third party Interference",10.8,765.0,0.16,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIDI",12.0,"1","BFE 1 - Ocean Beach",9.109299176165454,8.0,"Defective Equipment",12.186860000000001,853.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIDI",13.0,"2","LEV 11 - Leven St 11",3.046778016025233,2.0,"Third Party Interference - Vehicle Damage",6.77525,679.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIDI",14.0,"3","SPY 11 - Spey St 11",2.7736711432117818,1.0,"Defective Equipment",7.371579999999999,1355.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIDI",15.0,"4","SOU 9 - Southern 9",2.3918857916713496,1.0,"Third Party Interference - Vehicle Damage",5.212720000000002,689.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIFI",20.0,"1","BFE 1 - Ocean Beach",0.14687958469699072,8.0,"Defective Equipment",12.186860000000001,853.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIFI",21.0,"2","SPY 11 - Spey St 11",0.07657149305947544,1.0,"Defective Equipment",7.371579999999999,1355.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIFI",22.0,"3","SOU 9 - Southern 9",0.038878230448030654,1.0,"Third Party Interference - Vehicle Damage",5.212720000000002,689.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"SAIFI",23.0,"4","LEV 11 - Leven St 11",0.03848324116916821,2.0,"Third Party Interference - Vehicle Damage",6.77525,679.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"Customer impact",28.0,"1","BFE 1 - Ocean Beach",189.25556858147715,8.0,"Defective Equipment",12.186860000000001,853.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"Customer impact",29.0,"2","BFE 2 - Ocean Beach",184.1076923076923,4.0,"Other Cause",5.746539999999995,195.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"Customer impact",30.0,"3","LEV 13 - Leven St 13",115.17619047619047,2.0,"Third Party Interference - Vehicle Damage",11.73232,210.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Electricity Invercargill",2025.0,null,"Customer impact",31.0,"4","LEV 11 - Leven St 11",79.46284032376748,2.0,"Third Party Interference - Vehicle Damage",6.77525,679.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",12.0,"1","Mahia 3301",79.22962024391929,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",12.0,"1","Tiki Tiki 0206",32.372874169708304,38.0,"Vegetation",124.32700000000001,316.0,0.9946512020719553,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","SAIDI",12.0,"1","Mahia 3301",428.442068108885,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",13.0,"2","Raupunga 3101",33.692393349681254,34.0,"Vegetation",195.559,421.0,0.9981488962410321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",13.0,"2","Waimata 0903",26.482592924306914,40.0,"Vegetation",148.803,649.0,0.9761160729286372,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","SAIDI",13.0,"2","Raupunga 3101",182.19497508425036,34.0,"Vegetation",195.559,421.0,0.9981488962410321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",14.0,"3","Frasertown 3103",26.461467572706134,32.0,"Vegetation",189.407,481.0,0.9850375118131853,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",14.0,"3","Mata 0304",23.709473783415884,33.0,"Vegetation",117.595,274.0,0.9953994642629364,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",15.0,"4","Tiki Tiki 0206",26.386322620297147,38.0,"Vegetation",124.32700000000001,316.0,0.9946512020719553,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",15.0,"4","Rototahi 0403",20.014604042040983,27.0,"Unknown cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",16.0,"5","Dalton 0502",19.33023978903937,25.0,"Unknown cause",107.321,821.0,0.890934672617661,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",16.0,"5","Ruakituri 2003",25.533732672992603,26.0,"Defective Equipment",107.381,162.0,0.9987521069835446,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",17.0,"6","Inland 0301",17.41541433081923,13.0,"Vegetation",45.896,160.0,0.9924176398814711,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",17.0,"6","Waimata 0903",21.585301232740573,40.0,"Vegetation",148.803,649.0,0.9761160729286372,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","SAIFI",18.0,"1","Mahia 3301",4.012873754152824,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",18.0,"7","Mata 0304",19.325000959972694,33.0,"Vegetation",117.595,274.0,0.9953994642629364,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIDI",18.0,"7","Tiniroto 1003",15.924388750259567,38.0,"Vegetation",76.089,125.0,0.9992903047746717,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","SAIFI",19.0,"2","Raupunga 3101",1.038413621262458,34.0,"Unknown cause",195.559,421.0,0.9981488962410321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",19.0,"8","Rototahi 0403",16.313404753692126,27.0,"Unknown cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIDI",20.0,"9","Dalton 0502",15.755596513532959,25.0,"Unknown cause",107.321,821.0,0.890934672617661,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",23.0,"1","Waimata 0903",0.3211475950440478,40.0,"Vegetation",148.803,649.0,0.9761160729286372,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",24.0,"2","Elgin 0703",0.24878692231591837,4.0,"Defective Equipment",18.109,921.0,0.28803357446573524,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","Customer impact",24.0,"1","Ruakituri 2003",4104.783950634236,26.0,"Defective Equipment",107.381,162.0,0.9987521069835446,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Wairoa","Customer impact",25.0,"2","Mahia 3301",2199.7622601411404,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",25.0,"3","Crawford 1504",0.24647854148019038,5.0,"Defective Equipment",27.049,947.0,0.5149543421198566,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",25.0,"1","Mahia 3301",0.7420804054832388,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",26.0,"4","Rototahi 0403",0.2120412681961652,27.0,"Unknown cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",26.0,"2","Waimata 0903",0.26175939791882663,40.0,"Vegetation",148.803,649.0,0.9761160729286372,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",27.0,"3","Elgin 0703",0.20278001766309567,4.0,"Defective Equipment",18.109,921.0,0.28803357446573524,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",27.0,"5","Aberdeen 0609",0.18617798087341594,2.0,"Defective Equipment",41.872,1441.0,0.44576327856324033,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",28.0,"6","Muriwai 0905",0.16502567484807087,35.0,"Wildlife",78.53099999999999,413.0,0.9606779488354918,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",28.0,"4","Crawford 1504",0.20089851399608338,5.0,"Defective Equipment",27.049,947.0,0.5149543421198566,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",29.0,"5","Raupunga 3101",0.1920285681373114,34.0,"Adverse Environment",195.559,421.0,0.9981488962410321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","SAIFI",29.0,"7","Dalton 0502",0.14250718424647854,25.0,"Unknown cause",107.321,821.0,0.890934672617661,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",30.0,"6","Rototahi 0403",0.17282955112698237,27.0,"Unknown Cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",31.0,"7","Borough One 3204",0.1613485389548055,6.0,"Adverse Weather",33.616,819.0,0.3871668253212756,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",32.0,"8","Brickworks 3201",0.15416810659294244,9.0,"Adverse Weather",38.548,616.0,0.6284891563764656,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"SAIFI",33.0,"9","Aberdeen 0609",0.151749030449641,2.0,"Defective Equipment",41.872,1441.0,0.44576327856324033,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",34.0,"1","Tiniroto 1003",2704.216000014078,38.0,"Vegetation",76.089,125.0,0.9992903047746717,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",35.0,"2","Inland 0301",2310.4812500018743,13.0,"Vegetation",45.896,160.0,0.9924176398814711,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",36.0,"3","Tiki Tiki 0206",2174.6170886088557,38.0,"Vegetation",124.32700000000001,316.0,0.9946512020719553,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",37.0,"4","Makarika 0204",1987.9380530992057,15.0,"Defective Equipment",40.970000000000006,113.0,0.9873810104954844,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",38.0,"1","Ruakituri 2003",4104.783950634236,26.0,"Defective Equipment",107.381,162.0,0.9987521069835446,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",38.0,"5","Rototahi 0403",1966.8981481500184,27.0,"Unknown cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",39.0,"2","Tiniroto 1003",2704.216000014078,38.0,"Vegetation",76.089,125.0,0.9992903047746717,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",39.0,"6","Mata 0304",1836.7919708049965,33.0,"Vegetation",117.595,274.0,0.9953994642629364,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",40.0,"3","Inland 0301",2310.4812500018743,13.0,"Vegetation",45.896,160.0,0.9924176398814711,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,"Gisborne","Customer impact",40.0,"7","Tauwhareparae 0404",1708.0479452012694,38.0,"Unknown cause",102.76,146.0,0.9957862981704942,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",41.0,"4","Mahia 3301",2199.7622601411404,31.0,"Defective Equipment",113.506,938.0,0.8691522915088189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",42.0,"5","Tiki Tiki 0206",2174.6170886088557,38.0,"Vegetation",124.32700000000001,316.0,0.9946512020719553,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",43.0,"6","Raupunga 3101",2084.2066508450107,34.0,"Unknown cause",195.559,421.0,0.9981488962410321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",44.0,"7","Makarika 0204",1987.9380530992057,15.0,"Defective Equipment",40.970000000000006,113.0,0.9873810104954844,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",45.0,"8","Rototahi 0403",1966.8981481500184,27.0,"Unknown cause",48.732,216.0,0.9729130755971436,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Firstlight Network",2025.0,null,"Customer impact",46.0,"9","Mata 0304",1836.7919708049965,33.0,"Vegetation",117.595,274.0,0.9953994642629364,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIDI",12.0,"1","WAIMANA",20.541259999999994,18.0,"Defective Equipment",186.72638999999972,1010.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIDI",13.0,"2","WAIHAU BAY",18.113509999999998,10.0,"Defective Equipment",96.5648800000002,701.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIDI",14.0,"3","DUNN ROAD",16.49379,4.0,"3rd Party interference",16.55961,181.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIDI",15.0,"4","RUATOKI",14.27965,17.0,"Defective Equipment",123.69424,658.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIDI",16.0,"5","HOSPITAL",8.137,5.0,"Defective Equipment",90.92874000000008,2020.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIFI",21.0,"1","WAIMANA",0.1829304,18.0,"Defective Equipment",186.72638999999972,1010.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIFI",22.0,"2","TE KAHA",0.15650630000000001,6.0,"Defective Equipment",46.44925999999995,477.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIFI",23.0,"3","RUATOKI",0.11435070000000003,17.0,"Defective Equipment",123.69424,658.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIFI",24.0,"4","PLATEAU",0.0911959,4.0,"Defective Equipment",26.86631999999999,531.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"SAIFI",25.0,"5","WAIHAU BAY",0.08827260000000002,10.0,"Defective Equipment",96.5648800000002,701.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"Customer impact",30.0,"1","DUNN ROAD",2362.65564738292,4.0,"3rd Party interference",16.55961,181.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"Customer impact",31.0,"2","WAIHAU BAY",671.3228795438347,10.0,"Defective Equipment",96.5648800000002,701.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"Customer impact",32.0,"3","RUATOKI",564.2188449848024,17.0,"Defective Equipment",123.69424,658.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"Customer impact",33.0,"4","WAIMANA",528.7653465346534,18.0,"Defective Equipment",186.72638999999972,1010.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Horizon Networks",2025.0,null,"Customer impact",34.0,"5","MINGINUI",505.6317567567568,6.0,"Defective Equipment",89.84785000000007,296.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",12.0,"1","KAI_6",6.62,11.0,"Third party interference",45.1,807.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",13.0,"2","W21",6.45,34.0,"Defective Equipment",71.1,281.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",14.0,"3","N34",5.21,7.0,"Third party interference",26.0,1025.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",15.0,"4","P25",5.08,21.0,"Defective Equipment",125.8,380.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",16.0,"5","X54",4.61,28.0,"Third party interference",144.1,1629.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",17.0,"6","SB1062",4.2,7.0,"Third party interference",17.0,710.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIDI",18.0,"7","SW66",4.07,38.0,"Defective Equipment",111.7,851.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",23.0,"1","SB1152",0.095,2.0,"Third party interference",10.8,1529.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",24.0,"2","Y23",0.066,9.0,"Human Error",48.2,1062.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",25.0,"3","SB1062",0.063,7.0,"Third party interference",17.0,710.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",26.0,"4","WPR_1172",0.056,1.0,"Third party interference",14.7,2618.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",27.0,"5","P25",0.051,21.0,"Defective Equipment",125.8,380.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",28.0,"6","N34",0.046,7.0,"Other cause",26.0,1025.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"SAIFI",29.0,"7","KAI_6",0.045,11.0,"Third party interference",45.1,807.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",34.0,"1","L52",1134.0,13.0,"Adverse Weather",35.8,80.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",35.0,"2","W21",1048.0,34.0,"Defective Equipment",71.1,281.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",36.0,"3","P25",610.0,21.0,"Wildlife",125.8,380.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",37.0,"4","T41",443.0,8.0,"Wildlife",65.4,227.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",38.0,"5","E80",434.0,6.0,"Other cause",47.1,64.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",39.0,"6","KAI_6",374.0,11.0,"Third party interference",45.1,807.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["MainPower NZ",2025.0,null,"Customer impact",40.0,"7","P55",309.0,29.0,"Wildlife",151.9,422.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",12.0,"1","REC1170-Sounds",17.70457054537426,35.0,"Lightning",268.4954819999996,1156.0,99.73250015432292,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",13.0,"2","CB45-French Pass",17.354382865974827,45.0,"Defective equipment",200.52405599999986,210.0,99.3273654907519,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",14.0,"3","CB109- Waikawa",6.986641642746743,18.0,"Unknown",141.8478080000003,2178.5,95.37697614615234,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",15.0,"4","REC1562-Ngakuta",4.7193272981526455,4.0,"Third party interference",21.20540099999998,444.5,94.30007006233939,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",16.0,"5","CB103 Havelock Canvastown",3.767939942592184,10.0,"Vegetation",64.84554299999999,589.5,87.04679980858518,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIDI",17.0,"6","CB1250-Richmond Brook",3.673916243468021,16.0,"Unknown",173.70245300000016,520.5,94.64569852677907,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",22.0,"1","CB45-French Pass",0.23861043644660343,45.0,"Defective equipment",200.52405599999986,210.0,99.3273654907519,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",23.0,"2","CB109- Waikawa",0.14079634945168173,18.0,"Unknown",141.8478080000003,2178.5,95.37697614615234,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",24.0,"3","CB2262-Awatere",0.0886141164348274,4.0,"Unknown",74.164995,1.0,94.30659841613961,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",25.0,"4","CB2032-Cobb Line",0.0673437844998896,2.0,"Unknown",55.105764000000036,0.0,96.76208463419545,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",26.0,"5","CB2152-Havelock",0.0641789946272172,1.0,"Unknown",61.90869700000002,1.0,94.33400447759381,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"SAIFI",27.0,"6","CB1088 - Omaka",0.05354382865974829,2.0,"Third party interference",24.045886,518.5,71.95325636992543,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",32.0,"1","CB172-Talleys",1480.0,1.0,"Third party interference",1.7017199999999995,1.0,40.78920151376256,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",33.0,"2","CB45-French Pass",795.2580101180439,45.0,"Defective equipment",200.52405599999986,210.0,99.3273654907519,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",34.0,"3","REC1391-Craiglochart",630.2307692307693,18.0,"Lightning",87.99017999999991,129.5,92.93044973882314,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",35.0,"4","CB1683 Causeway",288.82716049382714,3.0,"Defective equipment",7.160510000000001,81.5,96.07326852416935,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",36.0,"5","CB5184-Vernon",286.30232558139534,7.0,"Lightning",21.782395999999995,43.0,94.06390830466954,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Marlborough Lines",2025.0,null,"Customer impact",37.0,"6","CB1253-Grassmere",286.22857142857146,12.0,"Unknown",69.60567099999999,140.5,95.46677453910331,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIDI",12.0,"1","Kaiteriteri",10.248174012593017,7.0,"Cause unknown",42.2,1245.0,0.77,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIDI",13.0,"2","Isel",6.034596451058958,4.0,"Defective equipment",11.6,1132.0,0.86,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIDI",14.0,"3","Kohatu",5.943148254149972,7.0,"Defective equipment",79.4,415.0,0.85,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIDI",15.0,"4","Pohara",5.177378362907842,10.0,"Cause unknown",58.4,1130.0,0.9400000000000001,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIFI",20.0,"1","Whakarewa",0.07954207212364052,3.0,"Cause unknown",26.1,1160.0,0.9400000000000001,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIFI",21.0,"2","Kaiteriteri",0.0663537492844877,7.0,"Cause unknown",42.2,1245.0,0.77,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIFI",22.0,"3","Waverley St",0.06388093875214654,5.0,"Defective equipment",7.2,929.0,0.19,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"SAIFI",23.0,"4","Isel",0.05937034917000573,4.0,"Defective equipment",11.6,1132.0,0.86,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",28.0,"1","Kohatu",625.4626506024097,7.0,"Cause unknown",79.4,415.0,0.85,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",29.0,"2","Kaiteriteri",359.5092369477912,7.0,"Cause unknown",42.2,1245.0,0.77,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",30.0,"3","Isel",232.82773851590105,4.0,"Defective equipment",11.6,1132.0,0.86,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",31.0,"4","Pohara",200.1079646017699,10.0,"Defective equipment",58.4,1130.0,0.9400000000000001,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",32.0,"5","Whakarewa",131.01896551724138,3.0,"Cause unknown",26.1,1160.0,0.9400000000000001,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Tasman",2025.0,null,"Customer impact",33.0,"6","Waverley St",98.65123789020453,5.0,"Cause unknown",7.2,929.0,0.19,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",12.0,"1","409 Towey St",3.9,1.0,"8.0 Defective Equipment",8.55,1177.0,0.7135,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",13.0,"2","421 Island Cliff",3.05,8.0,"2.0 Vegetation",72.4,184.0,0.9771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",14.0,"3","406 Reed St",2.92,1.0,"6.0 Wildlife",7.6,1124.0,0.5996,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",15.0,"4","490 Ohau",2.21,2.0,"3.0 Adverse Weather",42.06,130.0,0.98,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",16.0,"5","413 Haka",1.84,6.0,"8.0 Defective Equipment",13.12,205.0,0.99,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIDI",17.0,"6","449 Ngapara",1.82,9.0,"8.0 Defective Equipment",47.64,215.0,0.99,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",22.0,"1","406 Reed St",0.1022,1.0,"6.0 Wildlife",7.6,1131.0,0.5996,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",23.0,"2","409 Towey St",0.0851,1.0,"8.0 Defective Equipment",8.55,1183.0,0.7135,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",24.0,"3","423 Omarama",0.0344,4.0,"8.0 Defective Equipment",64.71,400.0,0.97,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",25.0,"4","479 Waianakarua",0.0322,5.0,"8.0 Defective Equipment",61.3,228.0,0.9665,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",26.0,"5","421 Island Cliff",0.0277,8.0,"2.0 Vegetation",72.4,184.0,0.9771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"SAIFI",27.0,"6","416 Kakanui",0.0222,5.0,"5.0 Third Party Interference",37.0,588.0,0.98,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",32.0,"1","464 Aviemore",533.59,1.0,"8.0 Defective Equipment",27.9,34.0,0.92,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",33.0,"2","424 Quailburn",255.28,2.0,"8.0 Defective Equipment",54.9,80.0,0.98,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",34.0,"3","490 Ohau",233.66,2.0,"3.0 Adverse Weather",42.1,130.0,0.98,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",35.0,"4","421 Island Cliff",223.93,8.0,"2.0 Vegetation",72.4,186.0,0.9771,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",36.0,"5","491 Buscot",170.09,1.0,"8.0 Defective Equipment",12.1,22.0,0.99,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Network Waitaki",2025.0,null,"Customer impact",37.0,"6","413 Haka",121.2,6.0,"8.0 Defective Equipment",13.12,205.0,0.99,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",12.0,"1","Ruakaka CB7",8.092627976555542,8.0,"Defective Equipment",104.24069,1134.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",13.0,"2","Mareretu CB2",7.720659062326076,18.0,"Defective Equipment",113.40887,664.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",14.0,"3","Dargaville CB6",7.640026818070299,13.0,"Vegetation",133.13392000000002,1007.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",15.0,"4","Bream Bay CB1107",6.435379001382069,5.0,"Third Party Interference",21.73599,1649.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",16.0,"5","Dargaville CB2",6.242959222144961,18.0,"Vegetation",92.35824000000001,945.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",17.0,"6","Mangawhai North CB3",5.595397812317179,3.0,"Adverse Weather",36.7397,795.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",18.0,"7","Mareretu CB6",4.555714483182024,6.0,"Vegetation",43.48066,597.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIDI",19.0,"8","Ruawai CB1032",4.495316601610975,18.0,"Lightning",136.65228,644.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",24.0,"1","Dargaville CB2",0.1932920733685508,18.0,"Unknown",92.35824000000001,945.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",25.0,"2","Ruakaka CB2",0.1251184344394003,10.0,"Vegetation",59.48212,987.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",26.0,"3","Bream Bay CB1107",0.11729782080886057,5.0,"Third Party Interference",21.73599,1649.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",27.0,"4","Maungaturoto CB2",0.10824317277832579,17.0,"Defective Equipment",65.49558999999999,775.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",28.0,"5","Ruakaka CB7",0.09410834604352246,8.0,"Defective Equipment",104.24069,1134.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",29.0,"6","Poroti CB1032",0.08451088172800444,15.0,"Unknown",177.59318,769.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",30.0,"7","Mareretu CB2",0.08304209117733287,18.0,"Defective Equipment",113.40887,664.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"SAIFI",31.0,"8","Hikurangi CB1102",0.080342440864044,9.0,"Defective Equipment",85.53421,476.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",36.0,"1","Alexander St CB1",7336.384615384615,2.0,"Defective Equipment",0.10087,13.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",37.0,"2","Mareretu CB2",746.968373493976,18.0,"Defective Equipment",113.40887,664.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",38.0,"3","Kaiwaka CB1022",631.4041570438799,7.0,"Wildlife",30.7014,216.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",39.0,"4","Ruawai CB1022",495.17734724292103,16.0,"Defective Equipment",76.46118,335.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",40.0,"5","Mareretu CB6",490.9171548117155,6.0,"Vegetation",43.48066,597.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",41.0,"6","Dargaville CB6",486.7503722084367,13.0,"Vegetation",133.13392000000002,1007.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",42.0,"7","Ruakaka CB7",459.28162185985013,8.0,"Defective Equipment",104.24069,1134.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Northpower",2025.0,null,"Customer impact",43.0,"8","Mangawhai North CB3",453.2771841609051,3.0,"Adverse Weather",36.7397,795.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",12.0,"1","Castle Hill GXP Unit 642",1.3368547281863865,17.0,"Defective equipment",74.28278999999998,270.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",13.0,"2","Hawthornden Unit 29",1.0410883086762484,3.0,"Defective equipment",4.0373,628.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",14.0,"3","Brookside Unit 124",1.030374775977791,35.0,"Wildlife",79.85801000000006,503.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",15.0,"4","Duvauchelle Unit 123",0.8757818814351478,31.0,"Defective equipment",102.01220599999996,805.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",16.0,"5","Motukarara Unit 111",0.7926916048775345,12.0,"Defective equipment",66.05413,331.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",17.0,"6","Rolleston Unit 111",0.7778270724250623,8.0,"Defective equipment",39.39309999999999,539.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",18.0,"7","Motukarara Unit 112",0.6723565379344274,28.0,"Unknown",48.36509,288.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",19.0,"8","Weedons Unit 112",0.5818427803352426,14.0,"Defective equipment",60.87562400000001,616.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",20.0,"9","Rolleston Unit 123",0.5742216326387181,2.0,"Third Party Interference",13.258500000000002,869.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",21.0,"10","Belfast Unit 19",0.5302737463541484,18.0,"Third Party Interference",33.88404,1390.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",22.0,"11","Halswell Unit 4",0.4378843518290754,1.0,"Defective equipment",12.157199999999998,1622.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",23.0,"12","Little River Unit 111",0.40566468707172226,5.0,"Defective equipment",20.992458999999997,98.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",24.0,"13","Larcomb Unit 122",0.39134483606845416,1.0,"Third Party Interference",21.33074,1279.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIDI",25.0,"14","Larcomb Unit 112",0.3851995993955793,5.0,"Vegetation",41.85308000000002,423.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",30.0,"1","Hawthornden Unit 29",0.017126717503601927,3.0,"Defective equipment",4.0373,628.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",31.0,"2","Belfast Unit 19",0.012663843693994448,18.0,"Third Party Interference",33.88404,1390.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",32.0,"3","Heathcote Unit 7",0.011350458586639491,1.0,"Defective equipment",4.583939999999999,0.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",33.0,"4","Larcomb Unit 122",0.009110236497171171,1.0,"Third Party Interference",21.33074,1279.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",34.0,"5","Rolleston Unit 123",0.008903784657553503,2.0,"Third Party Interference",13.258500000000002,869.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",35.0,"6","Brookside Unit 124",0.008767614295252486,35.0,"Wildlife",79.85801000000006,503.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",36.0,"7","Weedons Unit 112",0.008398636539340056,14.0,"Defective equipment",60.87562400000001,616.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",37.0,"8","Rolleston Unit 111",0.00740151807991004,8.0,"Defective equipment",39.39309999999999,539.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",38.0,"9","Lincoln Unit 112",0.007238992163615279,1.0,"Third Party Interference",14.0496,1375.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",39.0,"10","Motukarara Unit 112",0.007181888463295498,28.0,"Unknown",48.36509,288.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",40.0,"11","Halswell Unit 4",0.007098429208981973,1.0,"Defective equipment",12.157199999999998,1622.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",41.0,"12","Prebbleton Unit 113",0.006461503320799803,21.0,"Defective equipment",44.36718000000003,353.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",42.0,"13","Weedons Unit 122",0.006395614435815441,13.0,"Defective equipment",57.72471000000002,536.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"SAIFI",43.0,"14","Dallington Unit 8",0.006145236672874864,1.0,"Defective equipment",7.100899999999998,1241.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",48.0,"1","Castle Hill GXP Unit 642",1127.1962962962964,17.0,"Defective equipment",74.28278999999998,270.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",49.0,"2","Little River Unit 111",942.3673469387755,5.0,"Defective equipment",20.992458999999997,98.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",50.0,"3","Motukarara Unit 111",545.1993957703927,12.0,"Defective equipment",66.05413,331.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",51.0,"4","Motukarara Unit 112",531.4791666666666,28.0,"Unknown",48.36509,288.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",52.0,"5","Duvauchelle Unit 122",504.19727891156464,5.0,"Defective equipment",28.922639000000007,147.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",53.0,"6","Brookside Unit 124",466.34393638170974,35.0,"Wildlife",79.85801000000006,503.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",54.0,"7","Hawthornden Unit 29",377.40445859872614,3.0,"Defective equipment",4.0373,628.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",55.0,"8","Rolleston Unit 111",328.52875695732837,8.0,"Defective equipment",39.39309999999999,539.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",56.0,"9","Bankside Unit 113",326.71590909090907,8.0,"Vegetation",28.50303399999999,88.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",57.0,"10","Killinchy Unit 112",324.7013888888889,6.0,"Third Party Interference",39.58065000000001,144.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",58.0,"11","Coleridge GXP Unit 1022",295.37404580152673,10.0,"Defective equipment",81.39307699999998,131.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",59.0,"12","Duvauchelle Unit 125",280.70588235294116,4.0,"Vegetation",12.663949999999996,34.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",60.0,"13","Highfield Unit 113",263.46715328467155,7.0,"Third Party Interference",44.98356000000002,137.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Orion NZ",2025.0,null,"Customer impact",61.0,"14","Duvauchelle Unit 123",247.67329192546583,31.0,"Defective equipment",102.01220599999996,805.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIDI",12.0,"1","RMK 8 - Remarkables 8",27.50750676839805,5.0,"Other Cause",10.15393,822.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",12.0,"1","ELD 3 - Elderlee 3",13.458210896478535,6.0,"Adverse Weather",31.54899999999999,625.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",12.0,"1","ELD 3 - Elderlee 3",17.847131723521244,6.0,"Adverse Weather",31.548470000000002,625.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",13.0,"2","WHL 4 - Waihola 4",17.546505685447233,7.0,"Vegetation",40.491910000000004,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",13.0,"2","WHL 4 - Waihola 4",13.23151404210216,7.0,"Vegetation",40.67705000000002,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIDI",13.0,"2","RMK 7 - Remarkables 7",7.674870785134125,3.0,"Cause Unknown",19.28155,1969.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIDI",14.0,"3","RMK 12 - Remarkables 12",0.21142013290671907,2.0,"Cause Unknown",4.47118,249.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",14.0,"3","WHL 2 - Waihola 2",15.62463268174224,7.0,"Vegetation",14.27658,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",14.0,"3","WHL 2 - Waihola 2",11.782263114793544,7.0,"Vegetation",14.182070000000005,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIDI",15.0,"4","RMK 11 - Remarkables 11",0.13807531380753138,1.0,"Other Cause",18.320990000000002,1021.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",15.0,"4","WAT 1 - Waitati 1",8.605231465870158,8.0,"Defective Equipment",33.47413999999999,476.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",15.0,"4","WAT 1 - Waitati 1",11.411524211064538,8.0,"Defective Equipment",33.47414,476.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",16.0,"5","OWA 1 - Owaka 1",9.03877603168529,8.0,"Adverse Weather",86.42429,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",16.0,"5","OWA 1 - Owaka 1",6.815983428874204,8.0,"Adverse Weather",86.43060999999999,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",17.0,"6","OWA 2 - Owaka 2",8.889868404241792,25.0,"Adverse Weather",59.13973,267.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",17.0,"6","OWA 2 - Owaka 2",6.703694782985734,25.0,"Adverse Weather",59.139810000000004,267.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",18.0,"7","CLI 2 - Clinton 2",8.578829692091341,16.0,"Human Error",133.10913,399.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",18.0,"7","CLI 2 - Clinton 2",6.296160701382507,15.0,"Human Error",133.11058000000014,399.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",19.0,"8","PML 3 - Port Molyneux 3",7.620480388399125,6.0,"Adverse Weather",13.619879999999998,340.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",19.0,"8","PML 3 - Port Molyneux 3",5.746471409990976,6.0,"Adverse Weather",13.591820000000004,340.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",20.0,"9","WAT 3 - Waitati 3",7.548358247093389,10.0,"Vegetation",29.447830000000003,326.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",20.0,"9","WAT 3 - Waitati 3",5.692085360566503,10.0,"Vegetation",29.90168999999999,326.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIFI",20.0,"1","RMK 8 - Remarkables 8",0.13462958405119324,5.0,"Other Cause",10.15393,822.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIFI",21.0,"2","RMK 7 - Remarkables 7",0.07186807777504287,3.0,"Cause Unknown",19.28155,1969.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",21.0,"10","WAT 2 - Waitati 2",7.414909927175143,5.0,"Cause Unknown",10.81238,267.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",21.0,"10","WAT 2 - Waitati 2",5.591454308974401,5.0,"Cause Unknown",10.812380000000003,267.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",22.0,"11","WHL 1 - Waihola 1",7.366807205826025,8.0,"Vegetation",40.87499,102.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIFI",22.0,"3","RMK 12 - Remarkables 12",0.0027073590942653203,2.0,"Cause Unknown",4.47118,249.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIDI",22.0,"11","WHL 1 - Waihola 1",5.555180885399054,8.0,"Vegetation",40.87499000000003,102.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",23.0,"12","OWA 3 - Owaka 3",6.482177079340711,5.0,"Adverse Weather",9.8361,218.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","SAIFI",23.0,"4","RMK 11 - Remarkables 11",0.0007383706620723603,1.0,"Other Cause",18.320990000000002,1021.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",24.0,"13","OWA 4 - Owaka 4",6.408649546441794,13.0,"Adverse Weather",79.72129,138.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",25.0,"14","RAN 1 - Ranfurly 1",5.553468761977792,13.0,"Defective Equipment",93.22799,540.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",26.0,"15","PAL 2 - Palmerston 2",5.374345215280353,11.0,"Cause Unknown",47.538940000000004,418.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",27.0,"16","PAL 1 - Palmerston 1",5.336016353647655,13.0,"Defective Equipment",92.75706,286.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",27.0,"1","PAL 2 - Palmerston 2",0.09937858278337247,11.0,"Cause Unknown",47.538939999999975,418.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",28.0,"2","CLI 2 - Clinton 2",0.08670937906450335,15.0,"Human Error",133.11058000000014,399.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","Customer impact",28.0,"1","RMK 8 - Remarkables 8",135.9647201946472,5.0,"Other Cause",10.15393,822.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",28.0,"17","LAW 3 - Lawrence 3",4.089306247604465,5.0,"Third Party Interference - Vehicle Damage",83.50965,258.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","Customer impact",29.0,"2","RMK 7 - Remarkables 7",15.836973082783139,3.0,"Cause Unknown",19.28155,1969.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",29.0,"3","PML 3 - Port Molyneux 3",0.08169950382966537,6.0,"Adverse Weather",13.591820000000004,340.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",29.0,"18","RAN 4 - Ranfurly 4",3.940015331544666,21.0,"Cause Unknown",55.413129999999995,132.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",30.0,"4","WAT 1 - Waitati 1",0.07505178476805344,8.0,"Defective Equipment",33.47413999999999,476.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","Customer impact",30.0,"3","RMK 12 - Remarkables 12",3.4497991967871484,2.0,"Cause Unknown",4.47118,249.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",30.0,"19","CLY 2 - Clydevale 2",3.7365529577104817,17.0,"Cause Unknown",89.07786,185.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",31.0,"5","OWA 2 - Owaka 2",0.07090900332386049,25.0,"Adverse Weather",59.139810000000004,267.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Lakeland Frankton","Customer impact",31.0,"4","RMK 11 - Remarkables 11",0.5491923641703378,1.0,"Other Cause",18.320990000000002,1021.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIDI",31.0,"20","MER 2 - Merton 2",3.7152165580681835,8.0,"Adverse Weather",25.056150000000002,491.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",32.0,"6","RAN 1 - Ranfurly 1",0.0648875186666033,13.0,"Defective Equipment",93.1572,540.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",33.0,"7","OWA 1 - Owaka 1",0.06127462787224899,8.0,"Adverse Weather",86.43060999999999,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",34.0,"8","WHL 4 - Waihola 4",0.060841080976926476,7.0,"Vegetation",40.67705000000002,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",35.0,"9","OWA 3 - Owaka 3",0.057180018305314106,5.0,"Adverse Weather",9.836099999999998,218.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",36.0,"10","WHL 2 - Waihola 2",0.054337877547088714,7.0,"Vegetation",14.182070000000005,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",36.0,"1","CLI 2 - Clinton 2",0.14047527788424316,16.0,"Human Error",133.10913,399.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",37.0,"2","PAL 2 - Palmerston 2",0.13178740258080665,11.0,"Cause Unknown",47.538940000000004,418.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"SAIFI",37.0,"11","OWA 4 - Owaka 4",0.051640252420637495,13.0,"Adverse Weather",79.72128999999981,138.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",38.0,"3","PML 3 - Port Molyneux 3",0.10834291554873901,6.0,"Adverse Weather",13.619879999999998,340.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",39.0,"4","WAT 1 - Waitati 1",0.09952727737319314,8.0,"Defective Equipment",33.47414,476.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",40.0,"5","OWA 2 - Owaka 2",0.09403347387249064,25.0,"Adverse Weather",59.13973,267.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",41.0,"6","RAN 1 - Ranfurly 1",0.08604829436565561,13.0,"Defective Equipment",93.22799,540.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",42.0,"1","HIN 2 - Hindon 2",1662.7924528301887,5.0,"Adverse Weather",19.06467,26.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",42.0,"7","OWA 1 - Owaka 1",0.0812571866615546,8.0,"Adverse Weather",86.42429,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",43.0,"2","WHL 1 - Waihola 1",1130.5882352941176,8.0,"Vegetation",40.87499000000003,102.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",43.0,"8","WHL 4 - Waihola 4",0.08068225373706248,7.0,"Vegetation",40.491910000000004,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",44.0,"9","OWA 3 - Owaka 3",0.07582726459690678,5.0,"Adverse Weather",9.8361,218.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",44.0,"3","FIN 3 - Finegand 3",915.7222222222222,7.0,"Defective Equipment",3.52595,18.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",45.0,"10","WHL 2 - Waihola 2",0.07205825986968065,7.0,"Vegetation",14.27658,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",45.0,"4","WHL 2 - Waihola 2",882.9891696750902,7.0,"Vegetation",14.182070000000005,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",46.0,"5","WHL 4 - Waihola 4",873.3640699523053,7.0,"Vegetation",40.67705000000002,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",46.0,"11","OWA 4 - Owaka 4",0.06848089945061855,13.0,"Adverse Weather",79.72129,138.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",47.0,"12","RAN 4 - Ranfurly 4",0.06356202887440818,21.0,"Cause Unknown",55.413129999999995,132.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",47.0,"6","OWA 4 - Owaka 4",726.963768115942,13.0,"Adverse Weather",79.72128999999981,138.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",48.0,"7","OWA 1 - Owaka 1",720.0661577608142,8.0,"Adverse Weather",86.43060999999999,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",48.0,"13","MER 5 - Merton 5",0.05921809122268992,3.0,"Adverse Weather",68.42278999999999,840.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",49.0,"14","WAT 2 - Waitati 2",0.05877092117030716,5.0,"Cause Unknown",10.81238,267.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",49.0,"8","MLN 3 - Milburn 3",652.5581395348837,10.0,"Vegetation",27.760900000000017,43.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",50.0,"9","OWA 5 - Owaka 5",633.5833333333334,8.0,"Adverse Weather",43.07901999999994,72.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",50.0,"15","RAN 3 - Ranfurly 3",0.05774881819343228,3.0,"Human Error",4.59131,436.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",51.0,"16","MER 2 - Merton 2",0.04874153570972237,8.0,"Adverse Weather",25.056150000000002,491.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",51.0,"10","CLK 1 - Clarks 1",594.5172413793103,9.0,"Adverse Weather",52.11424000000004,58.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",52.0,"17","CLI 1 - Clinton 1",0.048486009965503646,23.0,"Cause Unknown",99.14365,199.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,null,"Customer impact",52.0,"11","MID 4 - Middlemarch 4",541.1885714285714,7.0,"Adverse Environment",48.82970999999999,87.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",53.0,"18","CLY 2 - Clydevale 2",0.039542608917848415,17.0,"Cause Unknown",89.07786,185.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",54.0,"19","PAL 1 - Palmerston 1",0.03800945445253609,13.0,"Defective Equipment",92.75706,286.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","SAIFI",55.0,"20","CLI 3 - Clinton 3",0.036795707167497166,15.0,"Lightning",52.94628,106.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",60.0,"1","HIN 2 - Hindon 2",1662.7924528301887,5.0,"Adverse Weather",19.06467,26.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",61.0,"2","WHL 1 - Waihola 1",1130.5882352941176,8.0,"Vegetation",40.87499,102.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",62.0,"3","FIN 3 - Finegand 3",915.7222222222222,7.0,"Defective Equipment",3.52595,18.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",63.0,"4","WHL 2 - Waihola 2",882.9891696750902,7.0,"Vegetation",14.27658,277.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",64.0,"5","WHL 4 - Waihola 4",873.3640699523053,7.0,"Vegetation",40.491910000000004,314.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",65.0,"6","OWA 1 - Owaka 1",720.0661577608142,8.0,"Adverse Weather",86.42429,196.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",66.0,"7","OWA 4 - Owaka 4",726.963768115942,13.0,"Adverse Weather",79.72129,138.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",67.0,"8","MLN 3 - Milburn 3",652.5581395348837,10.0,"Vegetation",27.760900000000003,43.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",68.0,"9","OWA 5 - Owaka 5",633.5833333333334,8.0,"Adverse Weather",43.07902,72.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",69.0,"10","CLK 1 - Clarks 1",594.5172413793103,9.0,"Adverse Weather",52.114239999999995,58.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",70.0,"11","MID 4 - Middlemarch 4",541.1885714285714,7.0,"Adverse Environment",48.82778,87.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",71.0,"12","PML 2 - Port Molyneux 2",516.92,7.0,"Adverse Weather",23.91668,50.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",72.0,"13","OWA 2 - Owaka 2",520.2317757009346,25.0,"Adverse Weather",59.13973,267.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",73.0,"14","PKW W - Pukeawa W",483.4,4.0,"Cause Unknown",15.62388,25.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",74.0,"15","RAN 4 - Ranfurly 4",465.4867924528302,21.0,"Cause Unknown",55.413129999999995,132.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",75.0,"16","OWA 3 - Owaka 3",464.40274599542334,5.0,"Adverse Weather",9.8361,218.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",76.0,"17","HIN 3 - Hindon 3",440.92753623188406,4.0,"Cause Unknown",21.73248,34.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",77.0,"18","ELD 3 - Elderlee 3",447.0064,6.0,"Adverse Weather",31.548470000000002,625.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",78.0,"19","WAT 2 - Waitati 2",434.7303370786517,5.0,"Cause Unknown",10.81238,267.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["OtagoNet",2025.0,"Otago","Customer impact",79.0,"20","MLN 1 - Milburn 1",426.09090909090907,5.0,"Vegetation",10.08798,55.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",12.0,"1","CLOTON RD NORTH",1.889969740538,22.0,"Defective equipment (11);",72.96552894919,929.0,0.955178860857195,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",13.0,"2","POHANGINA",1.612448388775,32.0,"Lightning (10);",185.57030408430998,1303.0,0.976681641126998,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",14.0,"3","PARK RD",1.607829762979,22.0,"Defective equipment (9);",71.12285519951999,690.0,0.9418404599929799,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",15.0,"4","COAST ROAD",1.603942225923,6.0,"Defective equipment (4);",59.79752421943,189.0,0.976779719976118,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",16.0,"5","COOK DRIVE",1.566433867188,1.0,"Vegetation (1);",8.808476290009999,1167.0,0.382508613308213,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",17.0,"6","WAITOTARA",1.495620631489,36.0,"Defective equipment (10);",179.83683696481998,680.0,0.988522639980241,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",18.0,"7","BROOKLANDS 7",1.236554307466,11.0,"Defective equipment (3);",48.50788032767,893.0,0.948518398335672,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",19.0,"8","WESTMERE PEAT ST",1.19825172023,19.0,"Vegetation (6);",29.15429840037,359.0,0.85929025300441,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",20.0,"9","CASTLEPOINT",1.130559841899,10.0,"Defective equipment (6);",65.74024175078999,448.0,0.972252954836174,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",21.0,"10","HETHERINGTON RD",1.112957163272,7.0,"Defective equipment (5);",8.90062556207,1385.0,0.329891782811626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",22.0,"11","STRATHMORE",1.101714922278,28.0,"Defective equipment (14);",190.61328644518002,407.0,0.9826998933389229,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",23.0,"12","MAKINO",1.0670704374759998,4.0,"Defective equipment (3);",53.44253310777,1428.0,0.814574183635221,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",24.0,"13","MANGOREWA",1.054417210857,17.0,"Wildlife (8);",28.237951662799997,215.0,0.7348349504474101,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",25.0,"14","TARATA",0.935366532155,12.0,"Defective equipment (6);",48.13302264248,156.0,0.974367726374384,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",26.0,"15","PURANGI",0.925972034962,4.0,"Vegetation (1);",34.68802127136,1283.0,0.49684932032458595,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",27.0,"16","KAIHERE",0.9070504183879999,16.0,"Wildlife (7);",60.744349787649995,447.0,0.970345346246544,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",28.0,"17","OTAHU RD",0.906127639104,3.0,"Defective equipment (2);",6.80875891808,1133.0,0.567589095138615,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",29.0,"18","WHAKAMARAMA",0.861569896167,4.0,"Vegetation (2);",41.57327361826,576.0,0.807055690697717,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",30.0,"19","SMITH ST",0.852271264475,4.0,"Defective equipment (2);",9.91744792712,874.0,0.552598342162557,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",31.0,"20","KAIMAI DRIVE",0.826095197495,19.0,"Vegetation (6);",69.78478380016,637.0,0.828295415962548,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",32.0,"21","KUAOTUNU",0.808788091478,7.0,"Third party interference (3);",51.915804456509996,1097.0,0.571503785827776,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",33.0,"22","HUIROA",0.791407226034,9.0,"Lightning (3);",59.77141244964,172.0,0.9811213315805319,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",34.0,"23","MAKETU",0.7897785125,5.0,"Vegetation (3);",24.97437374423,779.0,0.790997051064156,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",35.0,"24","WHIRITOA",0.764557493935,4.0,"Defective equipment (3);",22.660921780640003,736.0,0.81349577268076,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",36.0,"25","MAIN RD MOTONUI",0.763982550946,31.0,"Lightning (11);",170.65044804401,1085.0,0.9701427840879969,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",37.0,"26","WESTMERE GLADSTONE",0.738313285308,13.0,"Defective equipment (6);",94.69486729514,201.0,0.991335171833626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",38.0,"27","WAIHI NORTH",0.728650452905,17.0,"Defective equipment (7);",59.08684312827,828.0,0.856205256025179,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",39.0,"28","CORNFOOT ST",0.700682698124,2.0,"Defective equipment (1);",10.070938597980001,999.0,0.8415826423695999,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",40.0,"29","COLOGNE ST",0.652607343242,13.0,"Defective equipment (6);",92.45444173019,725.0,0.972666454686678,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",41.0,"30","MAKIRIKIRI",0.645981087704,15.0,"Vegetation (8);",166.74572381175,919.0,0.9868626455528591,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",42.0,"31","WAVERLEY",0.624499132568,10.0,"Defective equipment (7);",23.55051700271,557.0,0.8882766218352139,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",43.0,"32","FORDELL",0.617977864366,14.0,"Vegetation (5);",137.62611504882,609.0,0.9985112009870559,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",44.0,"33","MANGAWEKA",0.607488088825,25.0,"Vegetation (6);",159.79315957394002,618.0,0.9957188849974931,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",45.0,"34","NGATEA",0.605270646101,5.0,"Defective equipment (3);",14.76603012132,464.0,0.77018131145891,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",46.0,"35","WILSON RD",0.596882024385,2.0,"Defective equipment (1);",5.21762298292,877.0,0.442788674517655,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",47.0,"36","MANGATEPARU",0.58945764779,10.0,"Defective equipment (5);",56.98216151812,450.0,0.958312615553297,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",48.0,"37","RAETIHI",0.582876643283,20.0,"Lightning (12);",185.54500639458,1068.0,0.984134885737857,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",49.0,"38","TAWHITI RD",0.57773194003,21.0,"Defective equipment (8);",70.24078573732,579.0,0.954418004136465,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",50.0,"39","PEAT ST INLAND",0.56903731778,1.0,"Vegetation (1);",4.47105240241,528.0,0.930083424631413,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",51.0,"40","TOKO",0.568782005345,8.0,"Lightning (2);",54.28874919735,294.0,0.999549023453626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",52.0,"41","IRIRANGI",0.566523870205,20.0,"Cause unknown (8);",82.05997210998,218.0,0.991848473039407,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",53.0,"42","HEADS RD",0.562309409436,4.0,"Defective equipment (2);",19.20798089943,1530.0,0.823455818260907,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",54.0,"43","CLOTON RD SOUTH",0.562184635222,14.0,"Cause unknown (4);",79.04371657966,693.0,0.972518882391482,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",55.0,"44","GILMOUR ST",0.55025257057,1.0,"Defective equipment (1);",6.76853982863,823.0,0.5666029574485411,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIDI",56.0,"45","TAIRUA NORTH",0.547050814619,10.0,"Defective equipment (7);",61.26347162251,1049.0,0.6421165082212871,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",61.0,"1","KAIHERE",0.03815921975500001,16.0,"Wildlife (7);",60.744349787649995,447.0,0.970345346246544,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",62.0,"2","CLOTON RD NORTH",0.028494571729,22.0,"Defective equipment (11);",72.96552894919,929.0,0.955178860857195,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",63.0,"3","HETHERINGTON RD",0.026541225803,7.0,"Defective equipment (5);",8.90062556207,1385.0,0.329891782811626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",64.0,"4","COOK DRIVE",0.025710777888,1.0,"Vegetation (1);",8.808476290009999,1167.0,0.382508613308213,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",65.0,"5","WESTMERE PEAT ST",0.02334358747,19.0,"Vegetation (6);",29.15429840037,359.0,0.85929025300441,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",66.0,"6","POHANGINA",0.020874315418,32.0,"Lightning (10);",185.57030408430998,1303.0,0.976681641126998,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",67.0,"7","BARRETT RD",0.018802334079,7.0,"Defective equipment (5);",25.67872984315,1279.0,0.47428421201287896,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",68.0,"8","WHIRITOA",0.018302961746,4.0,"Defective equipment (3);",22.660921780640003,736.0,0.81349577268076,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",69.0,"9","BROOKLANDS 7",0.016810362661,11.0,"Defective equipment (3);",48.50788032767,893.0,0.948518398335672,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",70.0,"10","KUAOTUNU",0.013701011156,7.0,"Third party interference (3);",51.915804456509996,1097.0,0.571503785827776,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",71.0,"11","HEADS RD",0.012338083347,4.0,"Defective equipment (2);",19.20798089943,1530.0,0.823455818260907,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",72.0,"12","PARK RD",0.012178063473,22.0,"Defective equipment (9);",71.12285519951999,690.0,0.9418404599929799,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",73.0,"13","KAIMAI DRIVE",0.012092535615,19.0,"Vegetation (6);",69.78478380016,637.0,0.828295415962548,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",74.0,"14","KATERE 8",0.009711550398,2.0,"Defective equipment (1);",12.83901172079,1758.0,0.561049160024972,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",75.0,"15","WELCOME BAY",0.008996978934,4.0,"Defective equipment (2);",13.017585581019999,1595.0,0.36926868302050697,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",76.0,"16","MAKINO",0.008996978933,4.0,"Defective equipment (3);",53.44253310777,1428.0,0.814574183635221,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",77.0,"17","PURANGI",0.008894897296,4.0,"Vegetation (1);",34.68802127136,1283.0,0.49684932032458595,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",78.0,"18","WILLOUGHBY ST",0.008784538769,4.0,"Human error (1);",6.25378297079,728.0,0.5584429756232541,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",79.0,"19","WYNDHAM ST",0.008671421279,1.0,"Third party interference (1);",9.97755769222,1394.0,0.802391697444416,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",80.0,"20","MANOEKA RD",0.00862175994,6.0,"Wildlife (2);",12.24495661773,819.0,0.368973003871497,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",81.0,"21","CLOTON RD SOUTH",0.008152736194,14.0,"Cause unknown (4);",79.04371657966,693.0,0.972518882391482,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",82.0,"22","DAIRY FACTORY",0.008100315887,30.0,"Lightning (12);",70.99693763886,359.0,0.973280617823554,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",83.0,"23","SMITH ST",0.007697507275,4.0,"Defective equipment (2);",9.91744792712,874.0,0.552598342162557,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",84.0,"24","SPRINGVALE",0.007462995405,2.0,"Vegetation (1);",13.6236639973,1916.0,0.639377274974362,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",85.0,"25","PYES PA",0.007443682658,9.0,"Defective equipment (3);",48.461181052810005,532.0,0.8187373454795189,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",86.0,"26","REVANS ST",0.007435405768,18.0,"Defective equipment (10);",61.03182487745,1235.0,0.9542116534427509,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",87.0,"27","SUMMERHILL",0.007195375976,3.0,"Defective equipment (3);",11.79084483142,1021.0,7.54723815573128e-05,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",88.0,"28","CASTLEPOINT",0.007096053298,10.0,"Defective equipment (6);",65.74024175078999,448.0,0.972252954836174,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",89.0,"29","RAILWAY ST",0.006872577283,5.0,"Cause unknown (3);",16.266566464780002,729.0,0.605739011920194,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",90.0,"30","MAKETU",0.006858782468,5.0,"Vegetation (3);",24.97437374423,779.0,0.790997051064156,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",91.0,"31","PEAT ST INLAND",0.006792567353,1.0,"Vegetation (1);",4.47105240241,528.0,0.930083424631413,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",92.0,"32","MANGOREWA",0.006654619184,17.0,"Wildlife (8);",28.237951662799997,215.0,0.7348349504474101,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",93.0,"33","NGATEA",0.006395276653,5.0,"Defective equipment (3);",14.76603012132,464.0,0.77018131145891,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",94.0,"34","TOTMANS RD",0.006301471901,13.0,"Third party interference (4);",92.86496632943,541.0,0.880801397687774,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",95.0,"35","OTAHU RD",0.006235256789,3.0,"Defective equipment (2);",6.80875891808,1133.0,0.567589095138615,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",96.0,"36","COROGLEN",0.006177318554,24.0,"Defective equipment (9);",129.95086701936,1164.0,0.866326374311823,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",97.0,"37","OPOUTERE",0.006141452037,12.0,"Defective equipment (4);",61.27723569576,1295.0,0.562165220404412,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",98.0,"38","WAIMAPU",0.006072477957,13.0,"Defective equipment (5);",70.95221182644,1010.0,0.822683552982886,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",99.0,"39","WARATAH ST",0.00596763736,3.0,"Defective equipment (2);",5.14236387638,824.0,0.0841607871251348,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",100.0,"40","WAITOTARA",0.005788304735,36.0,"Defective equipment (10);",179.83683696481998,680.0,0.988522639980241,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",101.0,"41","LINTON",0.005735884447,12.0,"Defective equipment (5);",64.5880272694,672.0,0.945461641457985,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",102.0,"42","TAWHITI RD",0.005733125475,21.0,"Defective equipment (8);",70.24078573732,579.0,0.954418004136465,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",103.0,"43","WEST TOWN",0.005523444289,2.0,"Third party interference (1);",20.27586906968,2015.0,0.585556513919991,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",104.0,"44","CORNFOOT ST",0.005515167399,2.0,"Defective equipment (1);",10.070938597980001,999.0,0.8415826423695999,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"SAIFI",105.0,"45","WAIHI NORTH",0.005440675386,17.0,"Defective equipment (7);",59.08684312827,830.0,0.856205256025179,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",110.0,"1","COUNTY WATER",3564.555555,2.0,"Cause unknown (1);",1.16249537043,9.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",111.0,"2","COAST ROAD",3075.962962,6.0,"Defective equipment (4);",59.79752421943,189.0,0.976779719976118,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",112.0,"3","TARATA",2173.25641,12.0,"Defective equipment (6);",48.13302264248,156.0,0.974367726374384,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",113.0,"4","MANGOREWA",1777.572093,17.0,"Wildlife (8);",28.237951662799997,215.0,0.7348349504474101,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",114.0,"5","HYNDS RD",1683.675213,1.0,"Defective equipment (1);",0.75837230407,117.0,0.31609487364384703,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",115.0,"6","HUIROA",1667.726744,9.0,"Lightning (3);",59.77141244964,172.0,0.9811213315805319,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",116.0,"7","BROOKLANDS",1350.348837,3.0,"Vegetation (1);",22.4206556374,43.0,1.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",117.0,"8","WESTMERE GLADSTONE",1331.373134,13.0,"Defective equipment (6);",94.69486729514,201.0,0.991335171833626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",118.0,"9","WESTMERE PEAT ST",1209.779944,19.0,"Vegetation (6);",29.15429840037,359.0,0.85929025300441,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",119.0,"10","WATERWORKS RD",1081.6024844720496,6.0,"Vegetation (3);",71.71738279973,161.0,0.999255482780666,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",120.0,"11","TUTURUMURI",986.005263,14.0,"Defective equipment (13);",79.89806859787001,190.0,0.971861154174258,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",121.0,"12","STRATHMORE",981.140049,28.0,"Defective equipment (14);",190.61328644518002,407.0,0.9826998933389229,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",122.0,"13","IRIRANGI",941.922018,20.0,"Cause unknown (8);",82.05997210998,218.0,0.991848473039407,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",123.0,"14","CASTLEPOINT",914.683035,10.0,"Defective equipment (6);",65.74024175078999,448.0,0.972252954836174,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",124.0,"15","KOPU",859.060606,4.0,"Defective equipment (2);",10.79439008217,99.0,0.846785167750069,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",125.0,"16","RAWHITIROA",846.263959,8.0,"Defective equipment (3);",56.04214577248,197.0,0.99454483238113,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",126.0,"17","PARK RD",844.588405,22.0,"Defective equipment (9);",71.12285519951999,690.0,0.9418404599929799,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",127.0,"18","WAITOTARA",797.197058,36.0,"Defective equipment (10);",179.83683696481998,680.0,0.988522639980241,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",128.0,"19","CLOTON RD NORTH",737.381054,22.0,"Defective equipment (11);",72.96552894919,929.0,0.955178860857195,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",129.0,"20","KAIHERE",735.4921700223714,16.0,"Wildlife (7);",60.744349787649995,447.0,0.970345346246544,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",130.0,"21","TOKO",701.217687,8.0,"Lightning (2);",54.28874919735,294.0,0.999549023453626,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",131.0,"22","WAITARA EAST TOWN",678.795698,1.0,"Defective equipment (1);",4.20538686851,93.0,0.9321537217642261,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",132.0,"23","MAURICEVILLE",649.608333,13.0,"Lightning (5);",69.584854609,240.0,0.9968803726667279,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",133.0,"24","PUTORINO",645.851648,18.0,"Wildlife (6);",46.63955925394,182.0,0.961437311562329,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",134.0,"25","BLACK STUMP",633.188976,6.0,"Cause unknown (2);",12.50752479284,127.0,0.587184523271482,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",135.0,"26","MAHOE",626.628378,7.0,"Defective equipment (4);",22.82219836721,148.0,0.984050518561657,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",136.0,"27","MATAKANA RD",609.859531,8.0,"Cause unknown (3);",41.581802399530005,299.0,0.6573544843116019,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",137.0,"28","PIRINOA",567.09,7.0,"Defective equipment (4);",39.78323640667,100.0,0.7723428594433931,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",138.0,"29","WHAKAMARAMA",542.152777,4.0,"Vegetation (2);",41.57327361826,576.0,0.807055690697717,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",139.0,"30","HUKANUI",532.665158,11.0,"Defective equipment (4);",56.81830877684,221.0,0.996788787651237,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",140.0,"31","OLD CAMBRIDGE RD",507.6307053941909,9.0,"Cause unknown (2);",61.89228551382,241.0,0.831381619927904,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",141.0,"32","COONOOR",502.165016,16.0,"Defective equipment (4);",99.70219416594,303.0,0.997175173661562,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",142.0,"33","BROOKLANDS 7",501.896976,11.0,"Defective equipment (3);",48.50788032767,893.0,0.948518398335672,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",143.0,"34","COOK DRIVE",486.514138,1.0,"Defective equipment (1);",8.808476290009999,1167.0,0.382508613308213,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",144.0,"35","TE ROTI",483.707462,15.0,"Defective equipment (8);",59.2239369842,335.0,0.9962842649625151,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",145.0,"36","OTAKEHO",482.053672,20.0,"Defective equipment (12);",45.24332762477,354.0,0.9887792808921939,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",146.0,"37","PORTLAND QUAY",481.676923,2.0,"Defective equipment (2);",8.78672214041,325.0,0.986288064303764,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",147.0,"38","PARIHAKA",477.493788,16.0,"Defective equipment (9);",57.23268847136,322.0,0.9935662148444371,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",148.0,"39","MANGATEPARU",474.78,10.0,"Defective equipment (5);",56.98216151812,450.0,0.958312615553297,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",149.0,"40","TE KIRI",473.297794,21.0,"Lightning (13);",56.63788037293,272.0,0.982982634170034,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",150.0,"41","NGATEA",472.808189,5.0,"Defective equipment (3);",14.76603012132,464.0,0.77018131145891,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",151.0,"42","KAIMAI DRIVE",470.053375,19.0,"Vegetation (6);",69.78478380016,637.0,0.828295415962548,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",152.0,"43","RANGIKURA",465.891089,21.0,"Lightning (7);",106.27021777464,303.0,0.996311441570194,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",153.0,"44","KATERE 11",452.421052,3.0,"Vegetation (1);",4.26540905486,95.0,0.45680136553842204,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Powerco",2025.0,null,"Customer impact",154.0,"45","POHANGINA",448.536454,32.0,"Lightning (10);",185.57030408430998,1303.0,0.976681641126998,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Scanpower",2025.0,null,"SAIDI",12.0,"1","Weber",26.095173331486453,15.0,"Vegetation",95.592,858.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Scanpower",2025.0,null,"SAIFI",20.0,"1","North",0.22720959134439656,11.0,"Vegetation",237.553,976.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Scanpower",2025.0,null,"Customer impact",28.0,"1","Weber",0.04229363586950802,15.0,"Vegetation",95.592,858.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Scanpower",2025.0,null,"Customer impact",29.0,"2","North",0.014585379288785026,11.0,"Vegetation",237.553,976.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",12.0,"1","Motuoapa",23.531323407150932,3.0,"2 Vegetation",2.25,505.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",13.0,"2","Northern",18.509981498776735,40.0,"9 Unknown",108.14,1172.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",14.0,"3","Oruatua",18.355099063835745,6.0,"9 Unknown",19.8,387.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",15.0,"4","Kuratau",13.460775043868306,16.0,"6 Wildlife",42.76,1358.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",16.0,"5","Oparure",8.573294970744055,18.0,"8 Defective Equipment",49.07,893.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",17.0,"6","Wharepapa",7.782333690529627,25.0,"9 Unknown",98.48,395.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIDI",18.0,"7","Coast",7.335491291290984,23.0,"8 Defective Equipment",75.71,287.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",23.0,"1","Northern",0.28409468732286713,40.0,"9 Unknown",108.14,1172.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",24.0,"2","Kuratau",0.21585776127356832,16.0,"6 Wildlife",42.76,1358.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",25.0,"3","Wharepapa",0.18260421788190329,25.0,"9 Unknown",98.48,395.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",26.0,"4","Maihiihi",0.18010303942713418,29.0,"8 Defective Equipment",114.23,961.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",27.0,"5","Oparure",0.1578205236925423,18.0,"8 Defective Equipment",49.07,893.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",28.0,"6","Gravel Scoop",0.14196054826116733,13.0,"8 Defective Equipment",97.72,524.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"SAIFI",29.0,"7","Rangipo / Hautu",0.13383186370162353,7.0,"9 Unknown",38.64,920.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",34.0,"1","Oruatua",1143.7700258415507,6.0,"9 Unknown",19.8,387.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",35.0,"2","Motuoapa",1123.7306930646923,3.0,"2 Vegetation",2.25,505.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",36.0,"3","Rural",731.832061073279,7.0,"8 Defective Equipment",7.33,131.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",37.0,"4","Coast",615.128919848331,23.0,"8 Defective Equipment",75.71,287.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",38.0,"5","Ongarue",583.7844036693189,51.0,"2 Vegetation",123.84,218.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",39.0,"6","Mahoenui",536.4722222999262,12.0,"8 Defective Equipment",27.11,72.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Lines Company",2025.0,null,"Customer impact",40.0,"7","Ohura",521.807692305655,36.0,"9 Unknown",134.2,260.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",12.0,"1","NGR 6 - North Gore 6",11.402834861419246,8.0,"Adverse Weather",13.373910000000011,1377.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",13.0,"2","TOK 1 - Tokanui 1",8.476446411634234,32.0,"Defective Equipment",112.1910599999998,335.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",14.0,"3","SGR 4 - South Gore 4",7.017520286647484,9.0,"Adverse Weather",13.33744,1274.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",15.0,"4","OTU 3 - Otautau 3",6.1112340604912125,10.0,"Cause Unknown",32.94042999999996,502.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",16.0,"5","AHL 5 - Athol 5",6.021077036568749,14.0,"Cause Unknown",112.09947999999999,537.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",17.0,"6","KEL 2 - Kelso 2",5.828459268626756,11.0,"Third Party Interference - Vandalism",101.26818000000006,702.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",18.0,"7","KEL 1 - Kelso 1",5.2886500158077,23.0,"Third Party Interference - Vehicle Damage",178.09252000000058,378.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",19.0,"8","ORA 4 -",5.267546632943259,17.0,"Human Error",66.75561999999994,480.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",20.0,"9","MAT 5 - Mataura 5",5.116397934450662,18.0,"Defective Equipment",62.68943,865.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",21.0,"10","RTN 7 - Riverton 7",4.954104752871741,31.0,"Defective Equipment",111.44453999999986,763.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",22.0,"11","RSD 1 - Riversdale 1",4.551823163663189,20.0,"Third Party Interference - Overhead Contact",136.1163399999999,363.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",23.0,"12","KEN 5 - Kennington 4",4.379017810095875,29.0,"Defective Equipment",130.90338000000014,555.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIDI",24.0,"13","GRD 3 - Gorge Rd 3",4.334360838866074,24.0,"Defective Equipment",77.03271000000008,181.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",29.0,"1","NGR 6 - North Gore 6",0.2683633681104555,8.0,"Adverse Weather",13.373910000000011,1377.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",30.0,"2","SGR 4 - South Gore 4",0.15873643165772225,9.0,"Adverse Weather",13.33744,1274.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",31.0,"3","SGR 5 - South Gore 5",0.11608177890189275,11.0,"Adverse Weather",7.8179700000000025,769.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",32.0,"4","MAT 5 - Mataura 5",0.10082727368532371,18.0,"Defective Equipment",62.68943,865.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",33.0,"5","OTA 2 - Otatara 2",0.09136895352513669,15.0,"Cause Unknown",20.314819999999997,786.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",34.0,"6","RTN 7 - Riverton 7",0.09002529244388449,31.0,"Defective Equipment",111.44453999999986,763.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",35.0,"7","OHA 4 - Ohai 4",0.08278006112340697,12.0,"Defective Equipment",77.20551000000005,539.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",36.0,"8","NGR 4 -",0.08259563705343118,4.0,"Adverse Weather",12.007469999999993,772.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",37.0,"9","OTU 3 - Otautau 3",0.08027716303087837,10.0,"Cause Unknown",32.94042999999996,502.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",38.0,"10","NGR 3 - North Gore 3",0.07131942248919707,35.0,"Defective Equipment",129.68371999999988,385.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",39.0,"11","TOK 1 - Tokanui 1",0.06789440404678951,32.0,"Defective Equipment",112.1910599999998,335.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",40.0,"12","RSD 1 - Riversdale 1",0.06309937822741893,20.0,"Third Party Interference - Overhead Contact",136.1163399999999,363.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"SAIFI",41.0,"13","TOK 2 - Tokonui 2",0.06125513752766134,35.0,"Defective Equipment",118.85413999999999,253.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",46.0,"1","TOK 1 - Tokanui 1",958.9627421758569,32.0,"Defective Equipment",112.1910599999998,335.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",47.0,"2","GRD 3 - Gorge Rd 3",908.9226519337017,24.0,"Defective Equipment",77.03271000000008,181.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",48.0,"3","GRD 1 - Gorge Rd 1",881.5339805825242,10.0,"Defective Equipment",25.61638000000001,51.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",49.0,"4","HGH 5 - Hedgehope 5",655.3781512605042,11.0,"Defective Equipment",30.592180000000003,59.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",50.0,"5","MAK 7 -",658.7352941176471,34.0,"Vegetation",70.8532899999999,238.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",51.0,"6","WTN 13 - Winton 13",617.1428571428571,13.0,"Wildlife",46.37913999999998,126.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",52.0,"7","MAT 3 - Mataura 3",610.586592178771,15.0,"Defective Equipment",105.98614999999981,179.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",53.0,"8","GRD 2 - Gorge Rd 2",596.0851063829788,11.0,"Defective Equipment",62.785389999999936,164.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",54.0,"9","OTU 2 - Otautau 2",558.0092165898618,9.0,"Cause Unknown",48.827660000000016,108.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",55.0,"10","LUM 1 - Lumsden 1",544.1304347826087,15.0,"Adverse Weather",122.32543000000008,207.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",56.0,"11","KEL 1 - Kelso 1",530.3461030383091,23.0,"Third Party Interference - Vehicle Damage",178.09252000000058,378.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",57.0,"12","GLM 1 - Glenham 1",523.3623978201634,20.0,"Defective Equipment",94.14724000000011,183.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["The Power Company",2025.0,null,"Customer impact",58.0,"13","TOK 2 - Tokonui 2",511.1715976331361,35.0,"Defective Equipment",118.85413999999999,253.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",12.0,"1","OPONONI",30.14699040314496,27.0,"Vegetation",107.483977378998,1115.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",13.0,"2","OXFORD STREET",26.904159980643385,41.0,"Third Party",132.649781692631,1915.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",14.0,"3","AWARUA",22.315257173190282,22.0,"Defective Equipment",100.627668912171,1072.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",15.0,"4","JOYCES ROAD",12.656091611394949,5.0,"Vegetation",28.2338194815804,1407.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",16.0,"5","TOKERAU",11.943435429872457,6.0,"Defective Equipment",98.7014959361767,1611.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",17.0,"6","RANGIAHUA",11.538533815138305,32.0,"Unknown",190.465239707103,827.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIDI",18.0,"7","MANGONUI",11.402693698529786,4.0,"Adverse Weather",25.2845660477587,1801.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",23.0,"1","OPONONI",0.511273153968653,27.0,"Vegetation",107.483977378998,1115.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",24.0,"2","AWARUA",0.22688793898248263,22.0,"Defective Equipment",100.627668912171,1072.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",25.0,"3","OXFORD STREET",0.19227223200067053,41.0,"Third Party",132.649781692631,1915.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",26.0,"4","TE KAO",0.16450143882882115,21.0,"Unknown",110.617558117857,670.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",27.0,"5","RANGIAHUA",0.1559417545491768,32.0,"Unknown",190.465239707103,827.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",28.0,"6","MANGONUI",0.15307462352974038,4.0,"Adverse Weather",25.2845660477587,1801.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"SAIFI",29.0,"7","PUKENUI SOUTH",0.1427374067555108,10.0,"Unknown",52.1518064222798,608.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",34.0,"1","OPONONI",967.7589484302849,27.0,"Vegetation",107.483977378998,1115.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",35.0,"2","AWARUA",745.0839552238806,22.0,"Defective Equipment",100.627668912171,1072.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",36.0,"3","BULLS GORGE",711.4554455445544,8.0,"Defective Equipment",30.7266447977828,202.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",37.0,"4","RAWENE",710.0095480458593,18.0,"Unknown",47.3702475674087,372.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",38.0,"5","TIMBER MILL",652.5,1.0,"Defective Equipment",1.0,4.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",39.0,"6","TE KAO",589.9167953805893,21.0,"Unknown",110.617558117857,670.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Top Energy",2025.0,null,"Customer impact",40.0,"7","RUSSELL EXPRESS",554.5017272181522,11.0,"Defective Equipment",105.017508489851,681.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",12.0,"1","Okere",3.5289970453314696,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",12.0,"1","Waimarama",1.7778251833930188,22.0,"Defective equipment",250.1786408924197,1147.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",12.0,"1","Okere",3.5289970453314696,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",13.0,"2","Rotoma",2.9921205960595447,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",13.0,"2","Twyford",1.4333179246596712,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",13.0,"2","Rotoma",2.9921205960595447,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",14.0,"3","Ngakuru",2.130027563014445,19.0,"Vegetation",185.78646344600938,817.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",14.0,"3","Haumoana",1.3506762132022345,7.0,"Vegetation",176.17017144687821,1321.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",14.0,"3","Ngakuru",2.130027563014445,19.0,"Vegetation",185.78646344600938,817.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",15.0,"4","Waiteti",1.845551621410063,8.0,"Unknown",50.68591313072665,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",15.0,"4","Pohokura",1.1806181127567807,10.0,"Vegetation",110.59762538806336,200.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",15.0,"4","Waiteti",1.845551621410063,8.0,"Unknown",50.68591313072665,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",16.0,"5","Omarunui",0.9657984825624194,14.0,"Unknown",137.10668296085288,556.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",16.0,"5","Dalbeth",1.5621200612821255,13.0,"Defective equipment",219.24741752430415,1389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",16.0,"5","Waimarama",1.7778251833930188,22.0,"Defective equipment",250.1786408924197,1147.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",17.0,"6","Valley",0.9257306596542013,18.0,"Vegetation",245.1471808776146,695.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",17.0,"6","Kaharoa",1.3375109932246112,10.0,"Vegetation",166.73867470954346,1148.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",17.0,"6","Dalbeth",1.5621200612821255,13.0,"Defective equipment",219.24741752430415,1389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",18.0,"7","Raureka",0.8998393133107903,3.0,"Third party interference",50.78619898372886,1024.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",18.0,"7","Rerewhakaaitu",1.2820556798888652,14.0,"Vegetation",115.61431641318634,322.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",18.0,"7","Twyford",1.4333179246596712,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",19.0,"8","Haumoana",1.3506762132022345,7.0,"Vegetation",176.17017144687821,1321.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",19.0,"8","Taupo North",1.2478910327705899,13.0,"Vegetation",284.0380059177648,1968.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",19.0,"8","Poukawa",0.7880743664283427,11.0,"Vegetation",164.9734335079639,636.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",20.0,"9","Kaharoa",1.3375109932246112,10.0,"Vegetation",166.73867470954346,1148.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",20.0,"9","Paora Hapi",1.1319029709394457,3.0,"Vegetation",57.56801275065905,1171.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",20.0,"9","Rissington",0.7319720110801944,23.0,"Unknown",86.08177533943199,177.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",21.0,"10","Rerewhakaaitu",1.2820556798888652,14.0,"Vegetation",115.61431641318634,322.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",21.0,"10","Puketapu",0.6907434831488714,11.0,"Unknown",103.47076390204558,424.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",21.0,"10","Owhata",1.1104431272766597,4.0,"Vegetation",61.788453555136826,981.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",22.0,"11","Heathcote",0.6549844754334959,4.0,"Unknown",58.502452780242955,940.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",22.0,"11","Taupo North",1.2478910327705899,13.0,"Vegetation",284.0380059177648,1968.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIDI",22.0,"11","Aquarius",1.0308585807868436,7.0,"Unknown",71.41446938357115,1069.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",23.0,"12","Avondale",0.5287653812310494,2.0,"Vegetation",51.69034456961227,1165.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",23.0,"12","Pohokura",1.1806181127567807,10.0,"Vegetation",110.59762538806336,200.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",24.0,"13","Korokipo",0.4919714311667894,9.0,"Unknown",62.858685857895544,320.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",24.0,"13","Paora Hapi",1.1319029709394457,3.0,"Vegetation",57.56801275065905,1171.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIDI",25.0,"14","Park Island",0.46744679478765044,6.0,"Vegetation",62.970417659945646,517.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",25.0,"14","Owhata",1.1104431272766597,4.0,"Vegetation",61.788453555136826,981.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",25.0,"1","Taupo North",0.07660473570160004,13.0,"Vegetation",284.0380059177648,1968.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",26.0,"15","Aquarius",1.0308585807868436,7.0,"Unknown",71.41446938357115,1069.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",26.0,"2","Rotoma",0.05105041405154949,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",27.0,"3","Okere",0.045834737074146634,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",27.0,"16","Waikato St",1.0277839404148417,11.0,"Unknown",142.22950896657247,685.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",28.0,"1","Twyford",0.04866301486093608,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",28.0,"17","Omarunui",0.9657984825624194,14.0,"Unknown",137.10668296085288,556.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",28.0,"4","Waiteti",0.04272363150867823,8.0,"Unknown",50.68591313072665,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",29.0,"5","Ngakuru",0.0401199522520162,19.0,"Vegetation",185.78646344600938,817.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",29.0,"18","Valley",0.9257306596542013,18.0,"Vegetation",245.1471808776146,695.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",29.0,"2","Heathcote",0.04321442088932699,4.0,"Unknown",58.502452780242955,940.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",30.0,"3","Waimarama",0.038955367280985226,22.0,"Defective equipment",250.1786408924197,1147.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",30.0,"6","Dalbeth",0.039762258296628106,13.0,"Defective equipment",219.24741752430415,1389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",30.0,"19","Raureka",0.8998393133107903,3.0,"Third party interference",50.78619898372886,1024.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",31.0,"7","Owhata",0.03314907935398807,4.0,"Vegetation",61.788453555136826,981.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",31.0,"4","Omarunui",0.03215086366453298,14.0,"Unknown",137.10668296085288,556.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",31.0,"20","Tutukau",0.8965223200029947,19.0,"Unknown",116.39680112064613,257.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",32.0,"5","Valley",0.03131069879257495,18.0,"Vegetation",245.1471808776146,695.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",32.0,"8","Aquarius",0.03162680042756905,7.0,"Unknown",71.41446938357115,1069.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",32.0,"21","Paradise",0.8802812173240332,6.0,"Vegetation",84.79477922092738,649.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",33.0,"6","Puketapu",0.02369098569640101,11.0,"Unknown",103.47076390204558,424.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",33.0,"9","Kaharoa",0.02912294273985251,10.0,"Vegetation",166.73867470954346,1148.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",33.0,"22","Waikite",0.8519298080930336,13.0,"Vegetation",157.99131466392407,415.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",34.0,"7","Haumoana",0.02276763618365505,7.0,"Vegetation",176.17017144687821,1321.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",34.0,"10","Broadlands",0.0290314396349858,14.0,"Unknown",152.7707439575938,331.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",34.0,"23","Tarawera",0.8260926582566995,5.0,"Vegetation",115.1772955803683,1103.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",35.0,"8","Poukawa",0.022243572946691128,11.0,"Vegetation",164.9734335079639,636.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","SAIFI",35.0,"11","Tutukau",0.027384383747384892,19.0,"Unknown",116.39680112064613,257.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIDI",35.0,"24","Taharepa",0.7959123063024842,2.0,"Third party interference",46.960555086452395,1028.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",36.0,"9","Elwood",0.020588198595011414,4.0,"Wildlife",59.93849535409341,814.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",37.0,"10","Taradale A",0.019748033723053376,2.0,"Unknown",32.46432367476073,765.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",38.0,"11","Rissington",0.019698122938580618,23.0,"Unknown",86.08177533943199,177.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",38.0,"1","Iwitahi",779.5718152000002,5.0,"Vegetation",61.456554363332586,55.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",38.0,"1","Taupo North",0.07660473570160004,13.0,"Vegetation",284.0380059177648,1968.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",39.0,"2","Mill",667.349998,3.0,"Third party interference",1.9112644004002122,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",39.0,"2","Rotoma",0.05105041405154949,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",39.0,"12","Korokipo",0.019689804474501825,9.0,"Unknown",62.858685857895544,320.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",40.0,"13","Bay View",0.018907868851095334,4.0,"Vegetation",66.02901329718519,775.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",40.0,"3","Rerewhakaaitu",478.63876562111807,14.0,"Vegetation",115.61431641318634,322.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",40.0,"3","Twyford",0.04866301486093608,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",41.0,"4","Okere",0.045834737074146634,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",41.0,"4","Whakatau 3",440.9138879444444,5.0,"Unknown",18.8771819530054,18.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","SAIFI",41.0,"14","Henderson",0.016087909528384684,3.0,"Third party interference",9.443116471860554,986.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",42.0,"5","Okere",430.9158103666836,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",42.0,"5","Heathcote",0.04321442088932699,4.0,"Unknown",58.502452780242955,940.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",43.0,"6","Waiteti",0.04272363150867823,8.0,"Unknown",50.68591313072665,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",43.0,"6","Tutukau",419.3579083190661,19.0,"Unknown",116.39680112064613,257.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",44.0,"7","Ngakuru",0.0401199522520162,19.0,"Vegetation",185.78646344600938,817.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",44.0,"1","Factory 6094",1733.4833319999998,3.0,"Human error",0.18011913466453489,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",44.0,"7","Whakatau 1",398.13333300000005,2.0,"Unknown",10.51582379601895,21.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",45.0,"8","Dalbeth",0.039762258296628106,13.0,"Defective equipment",219.24741752430415,1389.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",45.0,"8","Whakatau 2",398.133333,2.0,"Unknown",28.49060002604864,25.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",45.0,"2","Toronui",780.0404738571426,4.0,"Vegetation",3.658167854711402,7.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",46.0,"3","Pohokura",707.8674120498752,10.0,"Vegetation",110.59762538806336,200.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",46.0,"9","Rotoma",385.52656098070725,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",46.0,"9","Waimarama",0.038955367280985226,22.0,"Defective equipment",250.1786408924197,1147.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",47.0,"4","Anderson",584.9266663999999,1.0,"Other cause",4.338227550514039,5.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",47.0,"10","Hatepe",363.45318319101125,2.0,"Unknown",12.435321620248244,133.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",47.0,"10","Owhata",0.03314907935398807,4.0,"Vegetation",61.788453555136826,981.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",48.0,"5","Rissington",495.7388694422536,23.0,"Unknown",86.08177533943199,177.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",48.0,"11","Omarunui",0.03215086366453298,14.0,"Unknown",137.10668296085288,556.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Central Region","Customer impact",48.0,"11","Lochinver",357.3623652903226,2.0,"Unknown",20.844703892260725,15.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",49.0,"12","Aquarius",0.03162680042756905,7.0,"Unknown",71.41446938357115,1069.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",49.0,"6","Kaiwaka",350.5484520206186,4.0,"Vegetation",26.308531903698952,48.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",50.0,"13","Valley",0.03131069879257495,18.0,"Vegetation",245.1471808776146,695.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",50.0,"7","Hendley",322.9096901321587,9.0,"Vegetation",58.703144731573666,113.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",51.0,"8","Twyford",257.7495851219148,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",51.0,"14","Kaharoa",0.02912294273985251,10.0,"Vegetation",166.73867470954346,1148.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",52.0,"9","Oreka",244.7485187455621,5.0,"Other cause",25.818510244175773,84.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",52.0,"15","Broadlands",0.0290314396349858,14.0,"Unknown",152.7707439575938,331.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",53.0,"10","Omarunui",208.81831237769782,14.0,"Unknown",137.10668296085288,556.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",53.0,"16","Tutukau",0.027384383747384892,19.0,"Unknown",116.39680112064613,257.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",54.0,"17","Waikite",0.025595913970444497,13.0,"Vegetation",157.99131466392407,415.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",54.0,"11","Ridgemount",203.91311893617024,6.0,"Vegetation",77.9584084658808,141.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",55.0,"18","Puketapu",0.02369098569640101,11.0,"Unknown",103.47076390204558,424.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",55.0,"12","Puketapu",195.84288314858492,11.0,"Unknown",103.47076390204558,424.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",56.0,"13","Washpool",192.46873187603305,4.0,"Vegetation",42.72351007153834,121.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",56.0,"19","Haumoana",0.02276763618365505,7.0,"Vegetation",176.17017144687821,1321.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",57.0,"20","Poukawa",0.022243572946691128,11.0,"Vegetation",164.9734335079639,636.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,"Hawke's Bay","Customer impact",57.0,"14","Watties A",190.175,1.0,"Other cause",4.520930637776843,2.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",58.0,"21","Wharewaka",0.021561458892230143,3.0,"Vegetation",97.04013647152853,1022.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",59.0,"22","Elwood",0.020588198595011414,4.0,"Wildlife",59.93849535409341,814.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",60.0,"23","Taradale A",0.019748033723053376,2.0,"Unknown",32.46432367476073,765.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"SAIFI",61.0,"24","Rissington",0.019698122938580618,23.0,"Unknown",86.08177533943199,177.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",64.0,"1","Factory 6094",1733.4833319999998,3.0,"Human error",0.18011913466453489,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",65.0,"2","Toronui",780.0404738571426,4.0,"Vegetation",3.658167854711402,7.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",66.0,"3","Iwitahi",779.5718152000002,5.0,"Vegetation",61.456554363332586,55.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",67.0,"4","Pohokura",707.8674120498752,10.0,"Vegetation",110.59762538806336,200.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",68.0,"5","Mill",667.349998,3.0,"Third party interference",1.9112644004002122,1.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",69.0,"6","Anderson",584.9266663999999,1.0,"Other cause",4.338227550514039,5.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",70.0,"7","Rissington",495.7388694422536,23.0,"Unknown",86.08177533943199,177.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",71.0,"8","Rerewhakaaitu",478.63876562111807,14.0,"Vegetation",115.61431641318634,322.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",72.0,"9","Whakatau 3",440.9138879444444,5.0,"Unknown",18.8771819530054,18.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",73.0,"10","Okere",430.9158103666836,22.0,"Vegetation",159.90968302257727,984.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",74.0,"11","Tutukau",419.3579083190661,19.0,"Unknown",116.39680112064613,257.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",75.0,"12","Whakatau 1",398.13333300000005,2.0,"Unknown",10.51582379601895,21.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",76.0,"13","Whakatau 2",398.133333,2.0,"Unknown",28.49060002604864,25.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",77.0,"14","Rotoma",385.52656098070725,21.0,"Vegetation",140.65094072831033,933.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",78.0,"15","Hatepe",363.45318319101125,2.0,"Unknown",12.435321620248244,133.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",79.0,"16","Lochinver",357.3623652903226,2.0,"Unknown",20.844703892260725,15.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",80.0,"17","Kaiwaka",350.5484520206186,4.0,"Vegetation",26.308531903698952,48.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",81.0,"18","Rangitaiki",348.4666663728814,4.0,"Third party interference",22.4291892957314,29.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",82.0,"19","Hendley",322.9096901321587,9.0,"Vegetation",58.703144731573666,113.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",83.0,"20","Ngakuru",313.2234843718653,19.0,"Vegetation",185.78646344600938,817.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",84.0,"21","Waiteti",279.4232561612091,8.0,"Unknown",50.68591313072665,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",85.0,"22","Twyford",257.7495851219148,21.0,"Defective equipment",163.6678963267354,668.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",86.0,"23","Waikite",246.48451483754513,13.0,"Vegetation",157.99131466392407,415.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Unison Networks",2025.0,null,"Customer impact",87.0,"24","Oreka",244.7485187455621,5.0,"Other cause",25.818510244175773,84.5,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",12.0,"1","SWAN K07",3.187683942,45.0,"Defective equipment",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",12.0,"1","SWAN K07",7.792555865,45.0,"Defective equipment",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",12.0,"1","TAKA K13",2.835856398,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",13.0,"2","WAIH K03",2.772410252,15.0,"Vegetation",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",13.0,"2","HELE K05",6.113638248,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",13.0,"2","HELE K05",2.500892878,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",14.0,"3","TAKA K13",1.675798797,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",14.0,"3","SNEL K07",4.038438095,12.0,"Defective equipment",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",14.0,"3","TAKA K16",2.272902244,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",15.0,"4","CLEV R140",1.766608936,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",15.0,"4","SNEL K07",1.651995071,12.0,"Defective equipment",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",15.0,"4","SNEL K10",3.630376327,7.0,"Vegetation",51.23,685.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",16.0,"5","MEAS K19",1.744415008,6.0,"Defective equipment",20.67,2771.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",16.0,"5","WAIH K03",1.638306447,15.0,"Vegetation",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",16.0,"5","WAIM K02",3.078063247,23.0,"Defective equipment",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",17.0,"6","SHEL K06",1.624234975,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",17.0,"6","KKAP K04",2.775838098,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",17.0,"6","SNEL K10",1.485070177,7.0,"Vegetation",51.23,685.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",18.0,"7","TAKA K16",1.343131083,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",18.0,"7","REMU K10",1.599567476,2.0,"Defective equipment",10.83,1867.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",18.0,"7","WARK K13",2.560864974,51.0,"Defective equipment",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",19.0,"8","HVAL K13",2.444785452,19.0,"Defective equipment",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",19.0,"8","WAIH K05",1.552538384,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",19.0,"8","WAIM K02",1.259136676,23.0,"Defective equipment",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",20.0,"9","KKAP K04",1.135506013,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",20.0,"9","OREW K02",2.420507189,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",20.0,"9","HANS K02",1.514657221,1.0,"Defective equipment",6.13,924.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",21.0,"10","MKAU K12",1.477554608,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",21.0,"10","WARK K13",1.04756783,51.0,"Defective equipment",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",21.0,"10","WAIM K09",2.352140309,17.0,"Cause unknown",27.72,2079.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",22.0,"11","SPUR K02",2.270679585,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",22.0,"11","FBSH K05",1.363135263,3.0,"Third party interference",22.21,2941.0,11.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",22.0,"11","CLEV R140",1.043945957,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",23.0,"12","MEAS K19",1.030830966,6.0,"Defective equipment",20.67,2771.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",23.0,"12","BOMA K01",2.103739439,21.0,"Cause unknown",84.15,2499.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",23.0,"12","WAIH K02",1.276054359,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",24.0,"13","HVAL K13",1.000083079,19.0,"Defective equipment",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",24.0,"13","RANU K04",2.033213025,17.0,"Cause unknown",42.09,1849.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",24.0,"13","MANU K04",1.198340183,5.0,"Third party interference",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",25.0,"14","KKAP K03",2.026168095,26.0,"Adverse weather",73.14,745.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",25.0,"14","MARA K01",1.19771302,7.0,"Defective equipment",21.73,2471.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",25.0,"14","OREW K02",0.99015159,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",26.0,"15","ORAK K04",1.170742325,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",26.0,"15","WELL K07",2.010883244,42.0,"Defective equipment",121.81,1735.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",26.0,"15","WAIM K09",0.962184998,17.0,"Cause unknown",27.72,2079.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",27.0,"16","SHEL K06",0.959812713,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",27.0,"16","TAKA K12",1.127357287,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",27.0,"16","MKIN K11",2.00313971,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",28.0,"17","WELL K09",1.936580688,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",28.0,"17","BAIR K10",0.975875866,3.0,"Defective equipment",8.21,904.0,28.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",28.0,"17","REMU K10",0.945235899,2.0,"Defective equipment",10.83,1867.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",29.0,"18","PONS K08",0.948021192,2.0,"Defective equipment",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",29.0,"18","ATKI K06",1.935288236,7.0,"Adverse weather",8.88,773.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",29.0,"18","SPUR K02",0.928861946,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",30.0,"19","MANU K11",0.936121324,1.0,"Human error",4.61,704.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",30.0,"19","WAIH K05",0.91744483,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",30.0,"19","WAIM K05",1.913200515,17.0,"Defective equipment",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",31.0,"20","RIVE K09",1.857822274,20.0,"Defective equipment",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",31.0,"20","ROSE K08",0.894779946,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",31.0,"20","HANS K02",0.895059694,1.0,"Defective equipment",6.13,924.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",32.0,"21","MEAS K16",0.863043354,5.0,"Cause unknown",19.13,2544.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",32.0,"21","ORAT K03",1.658348752,13.0,"Defective equipment",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",32.0,"21","MKAU K12",0.873134576,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",33.0,"22","BAIR K13",0.848637551,4.0,"Defective equipment",12.8,2618.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",33.0,"22","BOMA K01",0.860571987,21.0,"Cause unknown",84.15,2499.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",33.0,"22","KKAP K02",1.609343396,19.0,"Defective equipment",72.11,709.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",34.0,"23","RANU K04",0.831722027,17.0,"Cause unknown",42.09,1849.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",34.0,"23","PAPA K10",0.823924086,3.0,"Third party interference",13.53,1598.0,16.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",34.0,"23","SABU K04",1.566597932,4.0,"Cause unknown",12.65,2241.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",35.0,"24","SPUR K05",1.454466114,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",35.0,"24","KKAP K03",0.828840187,26.0,"Adverse weather",73.14,745.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",35.0,"24","MARA K04",0.821474936,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",36.0,"25","MKAU K27",0.799326879,3.0,"Third party interference",9.4,1693.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",36.0,"25","BMON K04",1.196525222,2.0,"Third party interference",3.95,865.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",36.0,"25","WELL K07",0.822587907,42.0,"Defective equipment",121.81,1735.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",37.0,"26","WAIH K06",0.787378366,9.0,"Defective equipment",22.94,1220.0,67.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",37.0,"26","MKIN K11",0.819419994,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",37.0,"26","HAUR K01",1.183817959,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",38.0,"27","TPAP K08",0.76354347,6.0,"Third party interference",3.56,315.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",38.0,"27","FBSH K05",0.805520495,3.0,"Third party interference",22.21,2941.0,11.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",38.0,"27","LAIN K03",1.182404312,10.0,"Cause unknown",22.18,615.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",39.0,"28","WELL K09",0.792192868,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",39.0,"28","HAUR K04",1.171184891,2.0,"Third party interference",7.26,1234.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",39.0,"28","MANU K08",0.757439435,5.0,"Third party interference",18.53,2052.0,15.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",40.0,"29","ATKI K06",0.791664144,7.0,"Adverse weather",8.88,773.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",40.0,"29","MANU K12",0.740838565,6.0,"Third party interference",14.11,2404.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",40.0,"29","MANL K02",1.148671866,3.0,"Defective equipment",8.9,1106.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",41.0,"30","JAME K07",1.123433071,1.0,"Adverse weather",9.49,1043.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",41.0,"30","WAIM K05",0.782629047,17.0,"Defective equipment",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",41.0,"30","AVON K01",0.674902683,2.0,"Defective equipment",9.83,2048.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",42.0,"31","RIVE K09",0.759975349,20.0,"Defective equipment",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",42.0,"31","RIVE K04",1.123124563,4.0,"Vegetation",18.46,1221.0,69.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",42.0,"31","KING K12",0.670455779,2.0,"Cause unknown",4.06,810.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",43.0,"32","WSWA K06",0.668801367,3.0,"Defective equipment",9.67,1557.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",43.0,"32","LAIN K09",1.061423651,14.0,"Defective equipment",10.61,305.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",43.0,"32","WAIH K02",0.754061405,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",44.0,"33","MANU K04",0.708137778,5.0,"Third party interference",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",44.0,"33","WAIA K04",1.010981199,4.0,"Defective equipment",6.63,1185.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",44.0,"33","HOWI K10",0.645101644,2.0,"Defective equipment",6.16,1299.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",45.0,"34","TAKA K11",0.60762869,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",45.0,"34","MARA K01",0.707767157,7.0,"Defective equipment",21.73,2471.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",45.0,"34","WAIM K08",0.980802369,15.0,"Vegetation",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",46.0,"35","ORAK K04",0.691829314,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",46.0,"35","MWEL K03",0.606690636,5.0,"Defective equipment",12.31,1906.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",46.0,"35","HELE K09",0.949276384,26.0,"Defective equipment",55.98,643.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",47.0,"36","ORAT K03",0.678377115,13.0,"Defective equipment",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",47.0,"36","MALB K17",0.602722208,1.0,"Third party interference",2.6,547.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIDI",47.0,"36","WAIA K02",0.948784341,4.0,"Wildlife",5.96,947.0,43.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",48.0,"37","KING K02",0.569501507,3.0,"Wildlife",4.47,954.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",48.0,"37","TAKA K12",0.666191692,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",49.0,"38","KKAP K02",0.658330585,19.0,"Defective equipment",72.11,709.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",49.0,"38","HOWI K06",0.538202854,1.0,"Defective equipment",8.27,1111.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",50.0,"39","MEAS K12",0.528408847,2.0,"Adverse weather",6.12,1118.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",50.0,"1","WAIM K09",0.083847087,17.0,"Cause unknown",27.72,2079.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",50.0,"39","SABU K04",0.640844798,4.0,"Cause unknown",12.65,2241.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",51.0,"40","SPUR K05",0.594975383,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",51.0,"2","HELE K05",0.064512786,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",51.0,"40","NEWT K25",0.527030163,2.0,"Defective equipment",2.47,655.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",52.0,"41","BAIR K10",0.576676455,3.0,"Defective equipment",8.21,904.0,28.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",52.0,"3","SWAN K07",0.049110981,45.0,"Cause unknown",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",52.0,"41","NEWM K01",0.508769461,2.0,"Third party interference",6.06,1334.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",53.0,"42","PONS K08",0.560216229,2.0,"Defective equipment",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",53.0,"4","HVAL K13",0.044580899,19.0,"Vegetation",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",53.0,"42","BALM K04",0.494836723,2.0,"Defective equipment",6.64,1509.0,45.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",54.0,"43","MANU K11",0.553184215,1.0,"Human error",4.61,704.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",54.0,"5","BOMA K01",0.042526873,21.0,"Cause unknown",84.15,2499.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",54.0,"43","FBSH K13",0.4900546,15.0,"Vegetation",40.4,1489.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",55.0,"6","SABU K04",0.041409939,4.0,"Cause unknown",12.65,2241.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",55.0,"44","CHEV K05",0.469890786,1.0,"Wildlife",5.09,1196.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",55.0,"44","ROSE K08",0.528754268,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",56.0,"45","SHOW K10",0.461972855,2.0,"Defective equipment",12.9,1373.0,17.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",56.0,"45","MEAS K16",0.510000086,5.0,"Cause unknown",19.13,2544.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",56.0,"7","WELL K07",0.033263889,42.0,"Third party interference",121.81,1735.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",57.0,"8","SPUR K02",0.032576606,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",57.0,"46","MKAU K07",0.454757791,4.0,"Cause unknown",18.2,2234.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",57.0,"46","BAIR K13",0.501487243,4.0,"Defective equipment",12.8,2618.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",58.0,"47","BMON K04",0.489459962,2.0,"Third party interference",3.95,865.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",58.0,"47","SHOW K14",0.451995032,11.0,"Adverse weather",34.15,2053.0,50.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",58.0,"9","WAIM K05",0.030948151,17.0,"Lightning",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",59.0,"10","RIVE K09",0.030522439,20.0,"Third party interference",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",59.0,"48","PAPA K10",0.486883256,3.0,"Third party interference",13.53,1598.0,16.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",59.0,"48","MEAS K11",0.436361916,4.0,"Defective equipment",14.53,1575.0,40.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",60.0,"49","VICT K14",0.429236055,1.0,"Cause unknown",1.41,487.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",60.0,"11","TORB K11",0.028812024,4.0,"Defective equipment",13.6,1973.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",60.0,"49","MARA K04",0.48543591,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",61.0,"50","HAUR K01",0.484261829,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",61.0,"12","MKIN K11",0.024203966,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",61.0,"50","ONEH K08",0.422445393,1.0,"Defective equipment",3.81,1219.0,49.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",62.0,"51","OTAR K17",0.414076015,1.0,"Defective equipment",15.9,1701.0,6.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",62.0,"13","WARK K13",0.023571396,51.0,"Vegetation",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",62.0,"51","LAIN K03",0.483683555,10.0,"Cause unknown",22.18,615.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",63.0,"52","HAUR K04",0.479094045,2.0,"Third party interference",7.26,1234.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",63.0,"52","AVON K13",0.409188476,1.0,"Third party interference",9.49,2478.0,50.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",63.0,"14","SNEL K07",0.022306104,12.0,"Cause unknown",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",64.0,"53","REMU K14",0.40779628,1.0,"Defective equipment",4.51,940.0,45.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",64.0,"53","MKAU K27",0.472347976,3.0,"Third party interference",9.4,1693.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",64.0,"15","RANU K04",0.021677378,17.0,"Cause unknown",42.09,1849.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIDI",65.0,"54","KING K06",0.399032223,3.0,"Defective equipment",2.87,872.0,41.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",65.0,"16","SPUR K05",0.020790944,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",65.0,"54","MANL K02",0.469884697,3.0,"Defective equipment",8.9,1106.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",66.0,"55","WAIH K06",0.465287174,9.0,"Defective equipment",22.94,1220.0,67.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",66.0,"17","OREW K02",0.018276142,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",67.0,"18","BOMA K04",0.018256512,15.0,"Cause unknown",48.44,948.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",67.0,"56","JAME K07",0.45956031,1.0,"Adverse weather",9.49,1043.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",68.0,"1","WAIH K05",0.034394065,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",68.0,"19","KKAP K04",0.018096271,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",68.0,"57","RIVE K04",0.459434117,4.0,"Vegetation",18.46,1221.0,69.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",69.0,"58","TPAP K08",0.451202409,6.0,"Third party interference",3.56,315.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",69.0,"20","WAIM K02",0.017432487,23.0,"Vegetation",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",69.0,"2","MARA K01",0.028695421,7.0,"Defective equipment",21.73,2471.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",70.0,"59","MANU K08",0.447595335,5.0,"Third party interference",18.53,2052.0,15.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",70.0,"21","ATKI K03",0.017401234,5.0,"Adverse weather",10.5,960.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",70.0,"3","BAIR K13",0.027716823,4.0,"Defective equipment",12.8,2618.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",71.0,"60","MANU K12",0.437785341,6.0,"Third party interference",14.11,2404.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",71.0,"22","WAIM K08",0.017280189,15.0,"Lightning",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",71.0,"4","WAIH K03",0.026662559,15.0,"Defective equipment",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",72.0,"5","MEAS K19",0.025470406,6.0,"Defective equipment",20.67,2771.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",72.0,"61","LAIN K09",0.43419426,14.0,"Defective equipment",10.61,305.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",72.0,"23","WAIA K04",0.017061458,4.0,"Lightning",6.63,1185.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",73.0,"24","NLYN K07",0.016272655,5.0,"Wildlife",4.4,800.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",73.0,"62","WAIA K04",0.413559875,4.0,"Defective equipment",6.63,1185.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",73.0,"6","CLEV R140",0.024491976,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",74.0,"25","WARK K05",0.015682953,15.0,"Defective equipment",103.15,1816.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",74.0,"7","TAKA K12",0.020461309,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",74.0,"63","WAIM K08",0.401214717,15.0,"Vegetation",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",75.0,"8","MKAU K07",0.018230978,4.0,"Cause unknown",18.2,2234.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",75.0,"26","WAIA K02",0.015073767,4.0,"Lightning",5.96,947.0,43.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",75.0,"64","AVON K01",0.398821708,2.0,"Defective equipment",9.83,2048.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",76.0,"27","COAT K03",0.014753525,16.0,"Defective equipment",49.72,897.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",76.0,"9","WAIH K02",0.018142432,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",76.0,"65","KING K12",0.39619389,2.0,"Cause unknown",4.06,810.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",77.0,"10","FBSH K05",0.017084796,3.0,"Third party interference",22.21,2941.0,11.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",77.0,"28","ORAT K03",0.014683321,13.0,"Vegetation",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",77.0,"66","WSWA K06",0.395216247,3.0,"Defective equipment",9.67,1557.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",78.0,"11","SHEL K06",0.016773907,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",78.0,"29","HAUR K01",0.014644215,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",78.0,"67","HELE K09",0.388318394,26.0,"Defective equipment",55.98,643.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",79.0,"30","WELL K09",0.013749925,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",79.0,"12","TAKA K13",0.016560359,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",79.0,"68","WAIA K02",0.388117137,4.0,"Wildlife",5.96,947.0,43.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",80.0,"69","SABU K01",0.387724161,3.0,"Vegetation",5.85,1226.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",80.0,"31","BIRK K05",0.012984548,5.0,"Defective equipment",7.71,1501.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",80.0,"13","MEAS K16",0.016354915,5.0,"Human error",19.13,2544.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",81.0,"70","HOWI K10",0.38121132,2.0,"Defective equipment",6.16,1299.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",81.0,"14","WAIH K06",0.015535937,9.0,"Defective equipment",22.94,1220.0,67.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",81.0,"32","HPOI K07",0.012801017,6.0,"Defective equipment",17.1,1004.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",82.0,"71","TORB K11",0.378372644,4.0,"Defective equipment",13.6,1973.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",82.0,"33","WAIM K06",0.012679962,14.0,"Lightning",23.74,372.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",82.0,"15","MARA K04",0.014262653,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",83.0,"72","ATKI K09",0.374720843,3.0,"Defective equipment",8.05,1519.0,56.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",83.0,"34","HOBV K04",0.011731025,3.0,"Defective equipment",13.82,1009.0,1.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",83.0,"16","MKAU K12",0.012540553,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",84.0,"17","TAKA K16",0.012516246,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",84.0,"35","HVAL K03",0.01142248,3.0,"Defective equipment",12.09,1441.0,32.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",84.0,"73","BOMA K04",0.374477897,15.0,"Cause unknown",48.44,948.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","SAIFI",85.0,"36","WGAT K04",0.010953868,6.0,"Defective equipment",20.46,972.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",85.0,"74","LAIN K01",0.364824577,5.0,"Adverse weather",14.52,907.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",85.0,"18","MANU K08",0.012359439,5.0,"Defective equipment",18.53,2052.0,15.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",86.0,"75","TAKA K11",0.359067353,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",86.0,"19","AVON K01",0.010915875,2.0,"Defective equipment",9.83,2048.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",87.0,"20","MANU K12",0.009780508,6.0,"Third party interference",14.11,2404.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",87.0,"76","MWEL K03",0.358513021,5.0,"Defective equipment",12.31,1906.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",88.0,"77","MALB K17",0.356167953,1.0,"Third party interference",2.6,547.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",88.0,"1","WARK K08",2208.0,2.0,"Defective equipment",2.53,27.0,92.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",88.0,"21","WSWA K06",0.009437179,3.0,"Defective equipment",9.67,1557.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",89.0,"22","ROSE K08",0.009177656,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",89.0,"78","BMON K01",0.341290811,3.0,"Third party interference",6.01,966.0,60.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",89.0,"2","WAIM K02",2000.5381,23.0,"Defective equipment",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",90.0,"79","MANL K11",0.340097506,4.0,"Defective equipment",11.36,1006.0,50.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",90.0,"3","KKAP K04",1785.9799,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",90.0,"23","OTAR K17",0.008699196,1.0,"Defective equipment",15.9,1701.0,6.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",91.0,"4","SNEL K10",1365.1175,7.0,"Vegetation",51.23,685.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",91.0,"24","MANU K04",0.008239634,5.0,"Defective equipment",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",91.0,"80","HELE K02",0.339904208,11.0,"Defective equipment",43.08,556.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",92.0,"5","HELE K05",1282.1818,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",92.0,"25","BAIR K04",0.007815207,2.0,"Vegetation",8.23,1458.0,49.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",92.0,"81","KING K02",0.336536771,3.0,"Wildlife",4.47,954.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",93.0,"26","MKAU K27",0.007790882,3.0,"Third party interference",9.4,1693.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",93.0,"82","NLYN K07",0.333480831,5.0,"Wildlife",4.4,800.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",93.0,"6","WELL K03",958.7246,5.0,"Cause unknown",27.15,138.0,100.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",94.0,"7","SWAN K07",950.2243,45.0,"Defective equipment",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",94.0,"83","LAIN K07",0.329130956,4.0,"Vegetation",8.99,719.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",94.0,"27","FBSH K13",0.007720663,15.0,"Vegetation",40.4,1489.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",95.0,"28","TAKA K11",0.00745574,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",95.0,"8","LAIN K09",888.2451,14.0,"Defective equipment",10.61,305.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",95.0,"84","TRIA K10",0.327702815,3.0,"Defective equipment",5.66,885.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",96.0,"29","ORAK K04",0.007355655,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",96.0,"85","WELL K02",0.327463266,37.0,"Defective equipment",133.66,580.0,89.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",96.0,"9","ORAT K03",795.2434,13.0,"Defective equipment",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",97.0,"10","WELL K09",770.0435,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",97.0,"86","HOWI K06",0.318041388,1.0,"Defective equipment",8.27,1111.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",97.0,"30","ORAK K11",0.007204258,1.0,"Defective equipment",3.82,826.0,46.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",98.0,"87","KEEL K12",0.315832099,4.0,"Third party interference",7.21,1131.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",98.0,"11","KKAP K03",700.2011,26.0,"Adverse weather",73.14,745.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",98.0,"31","HOWI K10",0.006958267,2.0,"Defective equipment",6.16,1299.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",99.0,"12","ATKI K06",644.4434,7.0,"Adverse weather",8.88,773.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",99.0,"88","MEAS K12",0.312253791,2.0,"Adverse weather",6.12,1118.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",99.0,"32","KING K02",0.006655501,3.0,"Wildlife",4.47,954.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",100.0,"33","AVON K13",0.006620357,1.0,"Third party interference",9.49,2478.0,50.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",100.0,"13","KKAP K02",583.7266,19.0,"Defective equipment",72.11,709.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",100.0,"89","ATKI K02",0.311921517,4.0,"Vegetation",11.29,1122.0,60.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",101.0,"34","TPAP K16",0.00637976,4.0,"Vegetation",4.4,1055.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",101.0,"14","OREW K02",560.4241,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIDI",101.0,"90","NEWT K25",0.311439086,2.0,"Defective equipment",2.47,655.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",102.0,"35","PONS K08",0.006366236,2.0,"Third party interference",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",102.0,"15","WARK K13",534.8866,51.0,"Defective equipment",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",103.0,"16","WAIM K05",505.5944,17.0,"Defective equipment",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",103.0,"36","MANU K03",0.005903991,2.0,"Wildlife",13.86,2029.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",104.0,"1","WAIM K09",0.034299188,17.0,"Cause unknown",27.72,2079.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",104.0,"37","MEAS K12",0.005782333,2.0,"Adverse weather",6.12,1118.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",104.0,"17","SNEL K07",500.7937,12.0,"Defective equipment",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",105.0,"18","LAIN K03",493.9364,10.0,"Cause unknown",22.18,615.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",105.0,"38","AVON K11",0.00571206,5.0,"Defective equipment",10.8,1905.0,46.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",105.0,"2","HELE K05",0.026389631,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",106.0,"19","SPUR K02",480.9446,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",106.0,"3","WAIH K05",0.020324738,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",106.0,"39","BALM K04",0.005666094,2.0,"Defective equipment",6.64,1509.0,45.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",107.0,"40","MARA K05",0.005644545,9.0,"Defective equipment",24.68,521.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",107.0,"20","SPUR K03",462.0218,11.0,"Third party interference",15.06,411.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",107.0,"4","SWAN K07",0.02009006,45.0,"Cause unknown",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",108.0,"41","SHEL K04",0.005590394,1.0,"Defective equipment",10.86,2074.0,13.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",108.0,"5","HVAL K13",0.018236467,19.0,"Vegetation",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",108.0,"21","WAIM K08",451.723,15.0,"Vegetation",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",109.0,"6","BOMA K01",0.017396141,21.0,"Cause unknown",84.15,2499.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",109.0,"22","HELE K02",388.281,11.0,"Defective equipment",43.08,556.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",109.0,"42","PAPA K02",0.005530933,3.0,"Cause unknown",11.45,2329.0,42.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",110.0,"7","MARA K01",0.016957072,7.0,"Defective equipment",21.73,2471.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",110.0,"23","SPUR K05",387.1632,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",110.0,"43","PAPA K10",0.005525535,3.0,"Third party interference",13.53,1598.0,16.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",111.0,"24","HELE K09",378.0482,26.0,"Defective equipment",55.98,643.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",111.0,"8","SABU K04",0.016939465,4.0,"Cause unknown",12.65,2241.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",111.0,"44","MCEN K01",0.005379551,1.0,"Third party interference",17.46,2364.0,42.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",112.0,"9","BAIR K13",0.016378768,4.0,"Defective equipment",12.8,2618.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",112.0,"25","WAIM K06",371.8868,14.0,"Vegetation",23.74,372.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",112.0,"45","REMU K10",0.005352511,2.0,"Defective equipment",10.83,1867.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",113.0,"46","ROSE K15",0.005268713,2.0,"Third party interference",7.77,1962.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",113.0,"26","BMON K04",360.0458,2.0,"Third party interference",3.95,865.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",113.0,"10","WAIH K03",0.015755774,15.0,"Defective equipment",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",114.0,"27","WELL K02",357.7487,37.0,"Defective equipment",133.66,580.0,89.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",114.0,"11","MEAS K19",0.015051293,6.0,"Defective equipment",20.67,2771.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",114.0,"47","MEAS K11",0.005128142,4.0,"Defective equipment",14.53,1575.0,40.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",115.0,"48","ONEH K12",0.005103806,3.0,"Defective equipment",7.76,904.0,44.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",115.0,"12","CLEV R140",0.014473061,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",115.0,"28","HVAL K13",352.1069,19.0,"Defective equipment",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",116.0,"13","WELL K07",0.013607056,42.0,"Third party interference",121.81,1735.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",116.0,"29","MKIN K11",349.899,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",116.0,"49","KING K01",0.004884847,2.0,"Defective equipment",5.78,1108.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",117.0,"14","SPUR K02",0.013326049,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",117.0,"30","HAUR K01",344.483,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",117.0,"50","VICT K14",0.004874028,1.0,"Cause unknown",1.41,487.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",118.0,"51","FREE K65",0.00479023,1.0,"Third party interference",3.13,927.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",118.0,"15","WAIM K05",0.012659883,17.0,"Lightning",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",118.0,"31","RIVE K09",344.2402,20.0,"Defective equipment",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",119.0,"16","RIVE K09",0.012485763,20.0,"Third party interference",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",119.0,"52","MNAB K06",0.004782114,1.0,"Defective equipment",8.0,1786.0,19.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",119.0,"32","LAIN K08",340.6,3.0,"Vegetation",10.04,4.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",120.0,"17","TAKA K12",0.012091119,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",120.0,"53","KING K06",0.004744273,3.0,"Defective equipment",2.87,872.0,41.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",120.0,"33","RBEA K11",339.3087,6.0,"Defective equipment",8.2,546.0,24.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","SAIFI",121.0,"54","MEAS K17",0.00473887,1.0,"Defective equipment",8.24,1874.0,46.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",121.0,"18","TORB K11",0.011786075,4.0,"Defective equipment",13.6,1973.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",121.0,"34","COAT K05",324.5332,10.0,"Vegetation",30.53,382.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",122.0,"19","MKAU K07",0.010773265,4.0,"Cause unknown",18.2,2234.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",122.0,"35","GHIT K07",316.6624,2.0,"Defective equipment",5.61,311.0,52.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Northern","Customer impact",123.0,"36","BOMA K06",310.0,3.0,"Cause unknown",0.01,1.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",123.0,"20","WAIH K02",0.010720349,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",124.0,"1","BAIR K09",1251.8571,3.0,"Third party interference",1.6,7.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",124.0,"21","FBSH K05",0.010095963,3.0,"Third party interference",22.21,2941.0,11.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",125.0,"22","SHEL K06",0.009912235,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",125.0,"2","TPAP K08",905.2885,6.0,"Third party interference",3.56,315.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",126.0,"23","MKIN K11",0.009901088,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",126.0,"3","CLEV R134",790.7603,9.0,"Defective equipment",17.94,123.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",127.0,"24","TAKA K13",0.009786033,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",127.0,"4","FREE K62",729.7407,1.0,"Defective equipment",2.61,242.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",128.0,"5","TAKA K17",672.7484,7.0,"Third party interference",21.64,162.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",128.0,"25","MEAS K16",0.009664652,5.0,"Human error",19.13,2544.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",129.0,"6","BAIR K02",665.0,1.0,"Defective equipment",6.36,1.0,27.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",129.0,"26","WARK K13",0.009641949,51.0,"Vegetation",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",130.0,"27","WAIH K06",0.009180746,9.0,"Defective equipment",22.94,1220.0,67.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",130.0,"7","TAKA K13",640.8308,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",131.0,"28","SNEL K07",0.009124721,12.0,"Cause unknown",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",131.0,"8","CLEV R140",625.9617,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",132.0,"9","HANS K02",608.3626,1.0,"Defective equipment",6.13,924.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",132.0,"29","RANU K04",0.008867499,17.0,"Cause unknown",42.09,1849.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",133.0,"10","WEST K11",564.52,1.0,"Defective equipment",6.6,50.0,5.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",133.0,"30","SPUR K05",0.008504927,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",134.0,"11","PARN K11",518.2126,2.0,"Defective equipment",1.12,127.0,4.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",134.0,"31","MARA K04",0.008428271,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",135.0,"32","OREW K02",0.007475877,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",135.0,"12","WAIH K03",490.9382,15.0,"Vegetation",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",136.0,"33","BOMA K04",0.007468039,15.0,"Cause unknown",48.44,948.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",136.0,"13","MANU K11",490.4958,1.0,"Human error",4.61,704.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",137.0,"34","MKAU K12",0.007410615,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",137.0,"14","TAKA K16",458.4471,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",138.0,"35","KKAP K04",0.007402546,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",138.0,"15","MWES K02",453.0076,3.0,"Defective equipment",16.65,129.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",139.0,"36","TAKA K16",0.007396243,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",139.0,"16","WAIH K02",446.5828,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",140.0,"37","MANU K08",0.007303603,5.0,"Defective equipment",18.53,2052.0,15.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",140.0,"17","ORAK K04",424.1734,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",141.0,"38","WAIM K02",0.007131033,23.0,"Vegetation",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",141.0,"18","BAIR K10",412.5669,3.0,"Defective equipment",8.21,904.0,28.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",142.0,"19","MALB K17",406.8595,1.0,"Third party interference",2.6,547.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",142.0,"39","ATKI K03",0.00711827,5.0,"Adverse weather",10.5,960.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",143.0,"20","BAIR K07",347.6406,1.0,"Defective equipment",1.51,63.0,2.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",143.0,"40","WAIM K08",0.007068714,15.0,"Lightning",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",144.0,"41","WAIA K04",0.006979324,4.0,"Lightning",6.63,1185.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",144.0,"21","PONS K08",332.4095,2.0,"Defective equipment",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",145.0,"22","MKAU K12",323.4183,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",145.0,"42","NLYN K07",0.006656621,5.0,"Wildlife",4.4,800.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",146.0,"23","TAKA K12",319.3201,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",146.0,"43","AVON K01",0.00645054,2.0,"Defective equipment",9.83,2048.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",147.0,"24","VICT K14",318.8414,1.0,"Cause unknown",1.41,487.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",147.0,"44","WARK K05",0.006415338,15.0,"Defective equipment",103.15,1816.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",148.0,"45","WAIA K02",0.006166241,4.0,"Lightning",5.96,947.0,43.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",148.0,"25","KING K12",317.9679,2.0,"Cause unknown",4.06,810.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",149.0,"26","REMU K10",317.6125,2.0,"Defective equipment",10.83,1867.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",149.0,"46","COAT K03",0.006035186,16.0,"Defective equipment",49.72,897.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",150.0,"27","MARA K04",313.9256,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",150.0,"47","ORAT K03",0.006006505,13.0,"Vegetation",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",151.0,"28","QUAY K23",313.3971,1.0,"Defective equipment",1.72,115.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",151.0,"48","HAUR K01",0.005990493,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",152.0,"29","SHEL K06",313.099,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",152.0,"49","MANU K12",0.00577962,6.0,"Third party interference",14.11,2404.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",153.0,"30","NEWT K25",297.1936,2.0,"Defective equipment",2.47,655.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",153.0,"50","WELL K09",0.005624518,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",154.0,"51","WSWA K06",0.005576744,3.0,"Defective equipment",9.67,1557.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",154.0,"31","WAIH K05",293.7673,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",155.0,"52","ROSE K08",0.005423355,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",155.0,"32","MANU K04",276.5377,5.0,"Third party interference",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",156.0,"53","BIRK K05",0.005311559,5.0,"Defective equipment",7.71,1501.0,61.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",156.0,"33","WIRI K02",273.0677,2.0,"Wildlife",8.42,310.0,17.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",157.0,"34","ROSE K08",260.2178,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",157.0,"54","HPOI K07",0.005236503,6.0,"Defective equipment",17.1,1004.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",158.0,"35","TAKA K11",250.3051,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",158.0,"55","WAIM K06",0.005186895,14.0,"Lightning",23.74,372.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",159.0,"56","OTAR K17",0.005140651,1.0,"Defective equipment",15.9,1701.0,6.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",159.0,"36","WAIH K06",239.1355,9.0,"Defective equipment",22.94,1220.0,67.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",160.0,"37","MEAS K19",235.1655,6.0,"Defective equipment",20.67,2771.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",160.0,"57","MANU K04",0.004869064,5.0,"Defective equipment",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",161.0,"38","ORAK K13",231.4144,2.0,"Vegetation",2.59,548.0,3.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",161.0,"58","HOBV K04",0.004798803,3.0,"Defective equipment",13.82,1009.0,1.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",162.0,"39","QUAY K07",228.0,1.0,"Defective equipment",0.95,1.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",162.0,"59","HVAL K03",0.00467256,3.0,"Defective equipment",12.09,1441.0,32.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",163.0,"40","KING K02",219.4479,3.0,"Wildlife",4.47,954.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",163.0,"60","BAIR K04",0.004618255,2.0,"Vegetation",8.23,1458.0,49.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",164.0,"41","NEWM K30",213.5899,2.0,"Defective equipment",5.1,474.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",164.0,"61","MKAU K27",0.004603888,3.0,"Third party interference",9.4,1693.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",165.0,"62","FBSH K13",0.004562381,15.0,"Vegetation",40.4,1489.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",165.0,"42","PONS K12",210.8874,1.0,"Third party interference",4.06,616.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",166.0,"63","WGAT K04",0.004480855,6.0,"Defective equipment",20.46,972.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",166.0,"43","MARA K05",200.5513,9.0,"Defective equipment",24.68,521.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",167.0,"64","KKAP K02",0.004432873,19.0,"Defective equipment",72.11,709.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",167.0,"44","BAIR K03",199.6637,3.0,"Defective equipment",5.28,694.0,9.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",168.0,"45","PAPA K10",193.8842,3.0,"Third party interference",13.53,1598.0,16.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",168.0,"65","TAKA K11",0.004405765,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",169.0,"66","ATKI K06",0.004402614,7.0,"Vegetation",8.88,773.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",169.0,"46","GINN K02",187.8281,3.0,"Defective equipment",2.49,262.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",170.0,"67","ORAK K04",0.004346685,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",170.0,"47","HOWI K10",186.7261,2.0,"Defective equipment",6.16,1299.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",171.0,"48","MARA K01",180.0317,7.0,"Defective equipment",21.73,2471.0,33.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",171.0,"68","SABU K01",0.004303575,3.0,"Vegetation",5.85,1226.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",172.0,"69","HAUR K04",0.004301961,2.0,"Third party interference",7.26,1234.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",172.0,"49","MCEN K11",179.5941,1.0,"Human error",6.96,270.0,6.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",173.0,"70","KEEL K06",0.004290792,3.0,"Vegetation",6.83,833.0,28.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",173.0,"50","MEAS K12",179.0009,2.0,"Adverse weather",6.12,1118.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",174.0,"51","HOWI K06",178.8787,1.0,"Defective equipment",8.27,1111.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",174.0,"71","ORAK K11",0.004257235,1.0,"Defective equipment",3.82,826.0,46.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",175.0,"72","TRIA K10",0.004167777,3.0,"Defective equipment",5.66,885.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",175.0,"52","LIVE K11",178.3665,1.0,"Third party interference",0.95,130.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",176.0,"73","WARK K04",0.004145425,10.0,"Lightning",51.03,832.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",176.0,"53","MARA K08",177.0,3.0,"Defective equipment",0.79,41.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",177.0,"74","KEEL K12",0.004132651,4.0,"Cause unknown",7.21,1131.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,"Southern","Customer impact",177.0,"54","MKAU K27",175.4819,3.0,"Third party interference",9.4,1693.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",178.0,"75","HOWI K10",0.004111865,2.0,"Defective equipment",6.16,1299.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",179.0,"76","ECOA K04",0.004089497,2.0,"Cause unknown",6.6,1296.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",180.0,"77","TRIA K03",0.003992058,3.0,"Defective equipment",8.87,1051.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",181.0,"78","SIMP K08",0.003956913,6.0,"Cause unknown",10.11,1180.0,44.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",182.0,"79","KING K02",0.003932954,3.0,"Wildlife",4.47,954.0,58.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",183.0,"80","AVON K13",0.003912178,1.0,"Third party interference",9.49,2478.0,50.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",184.0,"81","ATKI K09",0.003869058,3.0,"Cause unknown",8.05,1519.0,56.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",185.0,"82","RIVE K04",0.003861058,4.0,"Cause unknown",18.46,1221.0,69.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",186.0,"83","TPAP K16",0.003770008,4.0,"Vegetation",4.4,1055.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",187.0,"84","PONS K08",0.003762024,2.0,"Third party interference",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",188.0,"85","BROW K11",0.003718905,2.0,"Lightning",9.24,1130.0,17.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",189.0,"86","WARK K12",0.003667747,20.0,"Defective equipment",60.08,983.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",190.0,"87","SUNS K02",0.003581513,4.0,"Defective equipment",6.77,1027.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",191.0,"88","HELE K09",0.003557532,26.0,"Defective equipment",55.98,643.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",192.0,"89","RBEA K11",0.003544767,6.0,"Defective equipment",8.2,546.0,24.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"SAIFI",193.0,"90","MANU K03",0.003488866,2.0,"Wildlife",13.86,2029.0,29.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",196.0,"1","WARK K08",2208.0,2.0,"Defective equipment",2.53,27.0,92.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",197.0,"2","WAIM K02",2000.5381,23.0,"Defective equipment",27.34,396.0,94.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",198.0,"3","KKAP K04",1785.9799,17.0,"Vegetation",61.99,400.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",199.0,"4","SNEL K10",1365.1175,7.0,"Vegetation",51.23,685.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",200.0,"5","HELE K05",1282.1818,56.0,"Defective equipment",122.52,1220.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",201.0,"6","BAIR K09",1251.8571,3.0,"Third party interference",1.6,7.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",202.0,"7","WELL K03",958.7246,5.0,"Cause unknown",27.15,138.0,100.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",203.0,"8","SWAN K07",950.2243,45.0,"Defective equipment",92.09,2140.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",204.0,"9","TPAP K08",905.2885,6.0,"Third party interference",3.56,315.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",205.0,"10","LAIN K09",888.2451,14.0,"Defective equipment",10.61,305.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",206.0,"11","ORAT K03",795.2434,13.0,"Defective equipment",16.22,530.0,75.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",207.0,"12","CLEV R134",790.7603,9.0,"Defective equipment",17.94,123.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",208.0,"13","WELL K09",770.0435,36.0,"Defective equipment",124.44,645.0,98.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",209.0,"14","FREE K62",729.7407,1.0,"Defective equipment",2.61,242.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",210.0,"15","KKAP K03",700.2011,26.0,"Adverse weather",73.14,745.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",211.0,"16","TAKA K17",672.7484,7.0,"Third party interference",21.64,162.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",212.0,"17","BAIR K02",665.0,1.0,"Defective equipment",6.36,1.0,27.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",213.0,"18","ATKI K06",644.4434,7.0,"Adverse weather",8.88,773.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",214.0,"19","TAKA K13",640.8308,5.0,"Third party interference",12.79,1656.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",215.0,"20","CLEV R140",625.9617,29.0,"Defective equipment",82.72,1061.0,90.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",216.0,"21","HANS K02",608.3626,1.0,"Defective equipment",6.13,924.0,35.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",217.0,"22","KKAP K02",583.7266,19.0,"Defective equipment",72.11,709.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",218.0,"23","WEST K11",564.52,1.0,"Defective equipment",6.6,50.0,5.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",219.0,"24","OREW K02",560.4241,15.0,"Vegetation",110.02,1135.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",220.0,"25","WARK K13",534.8866,51.0,"Defective equipment",200.57,1232.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",221.0,"26","PARN K11",518.2126,2.0,"Defective equipment",1.12,127.0,4.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",222.0,"27","WAIM K05",505.5944,17.0,"Defective equipment",51.8,850.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",223.0,"28","SNEL K07",500.7937,12.0,"Defective equipment",34.6,2075.0,57.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",224.0,"29","LAIN K03",493.9364,10.0,"Cause unknown",22.18,615.0,93.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",225.0,"30","WAIH K03",490.9382,15.0,"Vegetation",18.14,2091.0,79.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",226.0,"31","MANU K11",490.4958,1.0,"Human error",4.61,704.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",227.0,"32","SPUR K02",480.9446,15.0,"Vegetation",65.04,1233.0,64.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",228.0,"33","SPUR K03",462.0218,11.0,"Third party interference",15.06,411.0,73.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",229.0,"34","TAKA K16",458.4471,6.0,"Defective equipment",18.27,1846.0,22.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",230.0,"35","MWES K02",453.0076,3.0,"Defective equipment",16.65,129.0,38.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",231.0,"36","WAIM K08",451.723,15.0,"Vegetation",26.13,660.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",232.0,"37","WAIH K02",446.5828,20.0,"Defective equipment",82.95,1066.0,71.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",233.0,"38","ORAK K04",424.1734,2.0,"Defective equipment",5.25,1019.0,21.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",234.0,"39","BAIR K10",412.5669,3.0,"Defective equipment",8.21,904.0,28.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",235.0,"40","MALB K17",406.8595,1.0,"Third party interference",2.6,547.0,47.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",236.0,"41","HELE K02",388.281,11.0,"Defective equipment",43.08,556.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",237.0,"42","SPUR K05",387.1632,20.0,"Cause unknown",65.56,976.0,81.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",238.0,"43","HELE K09",378.0482,26.0,"Defective equipment",55.98,643.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",239.0,"44","WAIM K06",371.8868,14.0,"Vegetation",23.74,372.0,91.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",240.0,"45","BMON K04",360.0458,2.0,"Third party interference",3.95,865.0,78.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",241.0,"46","WELL K02",357.7487,37.0,"Defective equipment",133.66,580.0,89.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",242.0,"47","HVAL K13",352.1069,19.0,"Defective equipment",61.96,1775.0,87.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",243.0,"48","MKIN K11",349.899,7.0,"Vegetation",12.56,1468.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",244.0,"49","BAIR K07",347.6406,1.0,"Defective equipment",1.51,63.0,2.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",245.0,"50","HAUR K01",344.483,2.0,"Defective equipment",3.75,921.0,48.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",246.0,"51","RIVE K09",344.2402,20.0,"Defective equipment",56.0,1383.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",247.0,"52","LAIN K08",340.6,3.0,"Vegetation",10.04,4.0,95.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",248.0,"53","RBEA K11",339.3087,6.0,"Defective equipment",8.2,546.0,24.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",249.0,"54","PONS K08",332.4095,2.0,"Defective equipment",3.88,1041.0,12.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",250.0,"55","COAT K05",324.5332,10.0,"Vegetation",30.53,382.0,86.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",251.0,"56","MKAU K12",323.4183,4.0,"Third party interference",10.9,1709.0,37.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",252.0,"57","TAKA K12",319.3201,29.0,"Human error",61.66,1004.0,72.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",253.0,"58","VICT K14",318.8414,1.0,"Cause unknown",1.41,487.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",254.0,"59","KING K12",317.9679,2.0,"Cause unknown",4.06,810.0,26.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",255.0,"60","REMU K10",317.6125,2.0,"Defective equipment",10.83,1867.0,36.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",256.0,"61","GHIT K07",316.6624,2.0,"Defective equipment",5.61,311.0,52.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",257.0,"62","MARA K04",313.9256,18.0,"Defective equipment",36.3,958.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",258.0,"63","QUAY K23",313.3971,1.0,"Defective equipment",1.72,115.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",259.0,"64","SHEL K06",313.099,5.0,"Defective equipment",10.19,1943.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",260.0,"65","BOMA K06",310.0,3.0,"Cause unknown",0.01,1.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",261.0,"66","WELL K07",298.513,42.0,"Defective equipment",121.81,1735.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",262.0,"67","NEWT K25",297.1936,2.0,"Defective equipment",2.47,655.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",263.0,"68","WAIH K05",293.7673,11.0,"Defective equipment",34.03,1960.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",264.0,"69","WAIM K09",292.6735,17.0,"Cause unknown",27.72,2079.0,53.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",265.0,"70","RANU K04",288.9306,17.0,"Cause unknown",42.09,1849.0,84.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",266.0,"71","LAIN K07",286.5563,4.0,"Vegetation",8.99,719.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",267.0,"72","MANU K04",276.5377,5.0,"Third party interference",11.75,1628.0,39.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",268.0,"73","JAME K07",276.3516,1.0,"Adverse weather",9.49,1043.0,10.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",269.0,"74","COAT K11",273.1631,11.0,"Cause unknown",40.11,706.0,70.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",270.0,"75","WIRI K02",273.0677,2.0,"Wildlife",8.42,310.0,17.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",271.0,"76","SWAN K02",266.413,2.0,"Defective equipment",1.78,131.0,63.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",272.0,"77","MANL K02",265.7136,3.0,"Defective equipment",8.9,1106.0,68.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",273.0,"78","NLYN K07",262.9181,5.0,"Wildlife",4.4,800.0,62.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",274.0,"79","ROSE K08",260.2178,2.0,"Third party interference",7.69,1279.0,18.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",275.0,"80","WAIA K02",258.1923,4.0,"Wildlife",5.96,947.0,43.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",276.0,"81","NLYN K02",256.7556,2.0,"Third party interference",2.3,536.0,77.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",277.0,"82","WELL K08",250.3186,18.0,"Defective equipment",58.97,408.0,97.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",278.0,"83","TAKA K11",250.3051,17.0,"Third party interference",65.42,913.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",279.0,"84","LAIN K01",249.8665,5.0,"Adverse weather",14.52,907.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",280.0,"85","RDAL K03",248.0,1.0,"Lightning",1.72,1.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",281.0,"86","BOMA K04",247.5407,15.0,"Cause unknown",48.44,948.0,83.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",282.0,"87","TORB K10",246.0947,2.0,"Defective equipment",2.31,493.0,80.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",283.0,"88","FORR K03",245.3616,2.0,"Third party interference",3.72,729.0,54.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",284.0,"89","ORAT K05",240.2329,4.0,"Vegetation",8.91,219.0,88.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Vector Lines",2025.0,null,"Customer impact",285.0,"90","RIVE K04",239.8691,4.0,"Vegetation",18.46,1221.0,69.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",12.0,"1","RAGCB6",24.6270779,18.0,"Defective Equipment",21.8200581,1021.0,0.518,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",13.0,"2","TEUCB11",21.097160800000008,44.0,"Unknown",148.8822783,766.0,0.965,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",14.0,"3","RAGCB2",16.049260399999998,11.0,"Defective Equipment",5.15053789,787.0,0.693,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",15.0,"4","RAGCB4",12.931631099999999,11.0,"Adverse weather / Defective Equipment / Unknown",4.836522932,662.0,0.321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",16.0,"5","TEUCB12",9.0202516,19.0,"Vegetation / Defective Equipment",35.348722404206185,278.0,0.9939032853698484,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",17.0,"6","WEACB6",6.4334837,25.0,"Defective Equipment",157.9951716,674.0,0.982592937669242,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",18.0,"7","WHACB2",5.609259399999999,20.0,"Defective Equipment",40.74212093,476.0,0.8978478543826756,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",19.0,"8","CHACB9",4.1850499,21.0,"Unknown",61.36385239,1358.0,0.8107922596480909,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",20.0,"9","RAGCB5",4.0906938,8.0,"Defective Equipment",4.99819524,154.0,0.7645306272589704,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",21.0,"10","GORCB11",3.8470261999999997,23.0,"Third Party / Unknown",78.66456637,580.0,0.9509430526591994,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",22.0,"11","PEACB12",3.3649863000000004,23.0,"Defective Equipment",55.18546616,652.0,0.8039875637067555,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",23.0,"12","BORCB4",3.3600993,1.0,"Adverse weather",9.574661048,1404.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",24.0,"13","WEACB2",2.7191740000000006,32.0,"Wildlife",82.031165087,1112.0,0.9331023902783788,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",25.0,"14","WEACB3",2.6364244,42.0,"Unknown",121.913369266,787.0,0.9533703825903086,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",26.0,"15","CHACB12",2.5732071,3.0,"Defective Equipment",12.84907025,1482.0,0.1602152404762516,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",27.0,"16","SANCB4",2.5488832,5.0,"Third Party",10.183127318,1321.0,0.3109203641599799,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",28.0,"17","CHACB15",2.3310739,2.0,"Adverse weather / Defective Equipment",9.087482946,1234.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",29.0,"18","CHACB13",2.1014513,3.0,"Defective Equipment",9.399028719,1246.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",30.0,"19","BORCB7",2.0697578,2.0,"Adverse weather / Defective Equipment",11.51601121,1362.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIDI",31.0,"20","GORCB13",2.0243591,22.0,"Defective Equipment",81.377262602,634.0,0.912676358668455,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",36.0,"1","TEUCB11",0.1196791,44.0,"Unknown",148.8822783,766.0,0.965,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",37.0,"2","RAGCB6",0.0882981,18.0,"Defective Equipment",21.8200581,1021.0,0.518,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",38.0,"3","CHACB9",0.0642286,21.0,"Unknown",61.36385239,1358.0,0.8107922596480909,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",39.0,"4","RAGCB4",0.0520411,11.0,"Adverse weather / Defective Equipment / Unknown",4.836522932,662.0,0.321,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",40.0,"5","GORCB11",0.050336700000000005,23.0,"Third Party / Unknown",78.66456637,580.0,0.9509430526591994,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",41.0,"6","RAGCB2",0.04730190000000001,11.0,"Defective Equipment",5.15053789,787.0,0.6928604899555452,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",42.0,"7","LATCB3",0.038306599999999996,5.0,"Defective Equipment",6.34540011,911.0,0.35601267876550025,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",43.0,"8","WHACB2",0.036483999999999996,20.0,"Defective Equipment",40.74212093,476.0,0.8978478543826756,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",44.0,"9","CHACB12",0.0362178,3.0,"Defective Equipment",12.84907025,1482.0,0.1602152404762516,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",45.0,"10","PEACB12",0.035163700000000006,23.0,"Defective Equipment",55.18546616,652.0,0.8039875637067555,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",46.0,"11","CHACB5",0.0335676,8.0,"Defective Equipment",7.081702107,931.0,0.151113105695622,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",47.0,"12","NGACB5",0.0314787,8.0,"Defective Equipment",11.64708692,973.0,0.28364623057179006,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",48.0,"13","HORCB6",0.0305232,13.0,"Adverse weather",37.267955519,1320.0,0.8672079117278931,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",49.0,"14","SANCB4",0.030404900000000002,5.0,"Third Party",10.183127318,1321.0,0.3109203641599799,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",50.0,"15","FINCB1",0.028572300000000002,13.0,"Unknown",52.529713635,413.0,0.929599748045533,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",51.0,"16","NGACB2",0.027044999999999996,17.0,"Adverse weather",49.314127883000005,632.0,0.9220370973177978,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",52.0,"17","AVACB6",0.0268285,4.0,"Defective Equipment",7.864983975,1386.0,0.0006921809398855132,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",53.0,"18","TEUCB12",0.02520259999999999,19.0,"Vegetation / Defective Equipment",35.34872240420612,278.0,0.9939032853698503,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",54.0,"19","CHACB13",0.0247101,3.0,"Defective Equipment",9.399028719,1246.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"SAIFI",55.0,"20","WEACB3",0.0246813,42.0,"Unknown",121.913369266,787.0,0.9533703825903086,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",60.0,"1","TEUCB12",3293.267913669065,19.0,"Vegetation / Defective Equipment",35.348722404206185,278.0,0.9939032853698484,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",61.0,"2","TEUCB11",2795.428903394256,44.0,"Unknown",148.8822783,766.0,0.965,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",62.0,"3","RAGCB5",2696.0594155844155,8.0,"Defective Equipment",4.99819524,154.0,0.7645306272589704,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",63.0,"4","RAGCB6",2448.163095004897,18.0,"Defective Equipment",21.8200581,1021.0,0.518,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",64.0,"5","RAGCB3",2351.3490666666667,6.0,"Defective Equipment / Unknown",8.425874913,75.0,0.9510196441009046,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",65.0,"6","RAGCB2",2069.8243837357054,11.0,"Defective Equipment",5.15053789,787.0,0.6928604899555452,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",66.0,"7","RAGCB4",1982.661253776435,11.0,"Adverse weather / Defective Equipment / Unknown",4.836522932,662.0,0.3208904843046446,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",67.0,"8","WHACB2",1196.0567226890757,20.0,"Defective Equipment",40.74212093,476.0,0.8978478543826756,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",68.0,"9","WEACB6",968.8120326409495,25.0,"Defective Equipment",157.9951716,674.0,0.982592937669242,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",69.0,"10","TEUCB13",916.0625974025975,10.0,"Defective Equipment / Wildlife",22.518009371992996,77.0,0.9987312377604952,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",70.0,"11","NGACB6",742.6608421052631,9.0,"Unknown",14.18358811,95.0,0.7310851386532544,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",71.0,"12","GORCB11",673.2096896551724,23.0,"Third Party / Unknown",78.664566366,580.0,0.9509430527075537,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",72.0,"13","PEACB12",523.8282208588957,23.0,"Defective Equipment",55.18546616,652.0,0.8039875637067555,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",73.0,"14","PUKCB10",446.92142480211083,8.0,"Defective Equipment",31.7819244,379.0,0.566886324857031,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",74.0,"15","SILCB4",421.1641791044776,4.0,"Third Party",7.525619373,268.0,0.5795533696067517,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",75.0,"16","GORCB12",345.673640167364,12.0,"Lightning",52.532431292999995,478.0,0.9496220565494244,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",76.0,"17","WEACB3",340.01166454891995,42.0,"Unknown",121.913369266,787.0,0.9533703825903086,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",77.0,"18","PEACB18",337.2307692307692,4.0,"Defective Equipment",19.715187743,104.0,0.3646097271151916,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",78.0,"19","GORCB13",324.07946372239746,22.0,"Defective Equipment",81.377262602,634.0,0.912676358668455,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["WEL Networks",2025.0,null,"Customer impact",79.0,"20","CHACB9",312.7908983799706,21.0,"Unknown",61.36385239,1358.0,0.8107922596480909,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIDI",12.0,"1","T0022 Kawhia",30.64,29.0,"Defective Equipment",266.0,1383.0,0.94,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIDI",13.0,"2","C2742 Pencarrow",11.04,10.0,"Third Party Interference",12.0,1067.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIDI",14.0,"3","C2702 Rotoorangi",8.28,8.0,"Vegetation",102.0,1505.0,0.67,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIDI",15.0,"4","C2712 Cambridge North",7.51,1.0,"Defective Equipment",49.0,1044.0,0.01,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIFI",20.0,"1","T0022 Kawhia",0.18,29.0,"Defective Equipment",266.0,1383.0,0.94,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIFI",21.0,"2","C2772 French Pass",0.1,18.0,"Third Party Interference",66.0,1078.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIFI",22.0,"3","C2742 Pencarrow",0.09,10.0,"Vegetation",12.0,1067.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"SAIFI",23.0,"4","T2762 Pukeatua",0.09,14.0,"Unknown",194.0,1062.0,0.87,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"Customer impact",28.0,"1","T0022 Kawhia",649.0,29.0,"Defective Equipment",266.0,1383.0,0.94,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"Customer impact",29.0,"2","C2742 Pencarrow",304.0,10.0,"Third Party Interference",12.0,1067.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"Customer impact",30.0,"3","C2712 Cambridge North",210.0,1.0,"Defective Equipment",49.0,1044.0,0.01,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Waipa Networks",2025.0,null,"Customer impact",31.0,"4","C2772 French Pass",192.0,18.0,"Third Party Interference",66.0,1078.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",12.0,"1","Johnsonville 10",1.9617581175906595,13.0,"Cause Unkown",22.71532,961.0,0.8735452549204679,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",13.0,"2","Ngauranga 7",1.8137040478768784,2.0,"Defective Equipment",10.26154,1267.0,0.3614028693548922,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",14.0,"3","Brown Owl 3",1.7897525610693201,10.0,"Cause Unkown",27.07831000000002,1057.0,0.8183427990890126,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",15.0,"4","Porirua 2",1.363868270600227,2.0,"Defective Equipment",14.77142,1431.0,0.05423107595613691,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",16.0,"5","Hataitai 2",1.3230998707106634,2.0,"Defective Equipment",6.577189999999999,1383.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",17.0,"6","Naenae 12",1.3023203654699638,2.0,"Vegetation",4.856700000000001,865.0,0.6952642740955791,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",18.0,"7","Naenae 11",1.3000336189835064,4.0,"Human Error",6.241430000000003,1281.0,0.8424079097258161,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",19.0,"8","Kenepuru 12",1.1741798309178537,1.0,"Wildlife",3.075319999999999,493.0,0.778735221050167,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIDI",20.0,"9","Melling 6",0.9035566157253239,2.0,"Defective Equipment",5.376720000000001,755.0,0.2805093067892693,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",25.0,"1","Porirua 2",0.02402429626943475,2.0,"Defective Equipment",14.77142,1431.0,0.05423107595613691,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",26.0,"2","Johnsonville 10",0.018970128280676308,13.0,"Cause Unkown",22.71532,961.0,0.8735452549204679,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",27.0,"3","Karori 3",0.01847151081093332,11.0,"Cause Unkown",57.265879999999974,3801.0,0.4859693066796494,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",28.0,"4","Naenae 11",0.017870903404197454,4.0,"Human Error",6.241430000000003,1281.0,0.8424079097258161,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",29.0,"5","Hataitai 2",0.016216399981868454,2.0,"Defective Equipment",6.577189999999999,1383.0,0.0,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",30.0,"6","Korokoro 9",0.01434658447033226,2.0,"Defective Equipment",8.709639999999997,1227.0,0.28085546589755733,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",31.0,"7","Brown Owl 5",0.01296405421331762,3.0,"Vegetation",24.873780000000004,1079.0,0.5837231011933047,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",32.0,"8","Ngauranga 7",0.012771406554553284,2.0,"Defective Equipment",10.26154,1267.0,0.3614028693548922,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"SAIFI",33.0,"9","Brown Owl 3",0.011779837722678028,10.0,"Cause Unkown",27.07831000000002,1057.0,0.8183427990890126,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",38.0,"1","Tawa 2",1204.670940185539,8.0,"Cause Unkown",5.582140000000001,39.0,0.6407058941552881,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",39.0,"2","Kenepuru 12",420.3420892475257,1.0,"Wildlife",3.075319999999999,493.0,0.778735221050167,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",40.0,"3","Johnsonville 10",360.2775927755883,13.0,"Cause Unkown",22.71532,961.0,0.8735452549204679,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",41.0,"4","Brown Owl 3",298.8361873207211,10.0,"Cause Unkown",27.07831000000002,1057.0,0.8183427990890126,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",42.0,"5","Naenae 12",265.71551059082424,2.0,"Vegetation",4.856700000000001,865.0,0.6952642740955791,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",43.0,"6","Ngauranga 7",252.64167324522063,2.0,"Defective Equipment",10.26154,1267.0,0.3614028693548922,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",44.0,"7","Plimmerton 11",214.16806547623543,12.0,"Vegetation",59.86326000000005,560.0,0.8623073651518479,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",45.0,"8","Melling 6",211.21443708096817,2.0,"Defective Equipment",5.376720000000001,755.0,0.2805093067892693,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Wellington Electricity",2025.0,null,"Customer impact",46.0,"9","Naenae 11",179.1103304817807,4.0,"Human Error",6.241430000000003,1281.0,0.8424079097258161,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIDI",12.0,"1","GYM11",17.47,7.0,"Adverse Environment",41.71,1418.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIDI",13.0,"2","RFN5",13.67,6.0,"Third Party",93.48,875.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIDI",14.0,"3","WAT1",11.66,18.0,"Wildlife",60.87,220.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIFI",20.0,"1","GYM11",0.2,7.0,"Adverse Environment",41.71,1418.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIFI",21.0,"2","ALD4",0.16,26.0,"Wildlife",221.71,794.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"SAIFI",22.0,"3","FOX1",0.15,12.0,"Vegetation and Lightning",104.7,273.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"Customer impact",28.0,"1","WAT1",767.67,18.0,"Wildlife",60.87,220.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"Customer impact",29.0,"2","FOX1",598.24,12.0,"Vegetation and Lightning",104.7,273.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]
["Westpower",2025.0,null,"Customer impact",30.0,"3","HKK1012",507.07,15.0,"Adverse Weather",147.55,10.0,null,"10(vi): Worst-performing feeders (unplanned)",10.06,"Year end","SCHEDULE 10: REPORT ON NETWORK RELIABILITY"]